Air Conditioning and Heating Services In Treasure Island, FL
The Florida heat is nothing to play around with. We understand how crucial it is to have your AC working at full capacity to give you the most comfortable environment. That’s why AC repair is serious business and having a perfectly functioning air conditioner is so important. No matter how you may try to prevent any issues, it is bound to happen…There is no need to worry. Total Air Inc. provides expert air conditioning installations, AC preventative maintenance, and air conditioning repair in Treasure Island, FL and surrounding areas at an affordable rate
Treasure Island Air Conditioning Repair Experts
When the Florida heat pumps up, the last thing you need is for your air conditioning system to stop working. Sometimes your AC will act up and when it does, you can count on the quick and dependable AC repair service from Total Air Inc. We understand the importance of a fully functioning air conditioner and make your AC concerns a top priority.
At Total Air Inc., we are committed to keeping our customers in Treasure Island and throughout the Pinellas County area cool and comfortable. Our experienced and highly trained HVAC technicians will provide the prompt, high-quality air conditioning repair service needed to get your air conditioning systems up and running smoothly.
When it comes to Florida heat, AC repair is crucial for any situation, large or small. If your air conditioning unit is blowing hot air, making strange rattling sounds, or won’t turn on at all, give us a call at (727) 822-7700 . We will be there to solve any of your air conditioning problems.
Treasure Island, FL Central Air Conditioning FAQs
Replacement of an air conditioner in a family house might cost anywhere from $4,350 to $12,095. This covers the cost of labor as well as the cost of obtaining a permit. This range also includes variable-speed AC systems, as well as a variety of system sizes and levels of sophistication.
Your AC unit should be serviced twice a year, once in the fall and once in the spring. This is to guarantee that it is clean, its parts are in excellent working order, and it is performing at its best.
HVAC experts focus on your heater or furnace in the autumn so it's as ready as it can be for the winter. HVAC experts plan tune-ups for air conditioners in the spring after the weather has warmed up, so they're ready for the humidity and heat.
The first thing to consider is humidity. Indoors, high humidity levels result in excess wetness and dampness, both of which can be harmful to your health. Mold, mildew, and dust mites thrive in damp environments, aggravating allergies and asthma. Investing in a dehumidifier is one of the greatest ways to reduce humidity in your house. These devices will efficiently remove moisture from the air, hence removing contaminants like dust mites and mold.
for Treasure Island, FL
Our Reviews by City
Paul - Treasure Island, FL 33706
Peter - Treasure Island, FL 33706
Joann - Treasure Island, FL 33706
Response from Total Air, Inc.:
We are incredibly grateful that you took the time out to leave us a 5-Star review.
Nathan’s the best.
Wendy - Treasure Island, FL 33706
Prompt great service
Wendy - Treasure Island, FL 33706
Paige - Treasure Island, FL 33706
Wade was great. Professional and friendly. I give him the highest marks. (I dont do Google, sorry)
Joyce - Treasure Island, FL 33706
Morse - Treasure Island, FL 33706
Change address to be: Margaret Morse 10355 Paradise Blvd #701 (706 no longer owned by me) Treasure Island
Blake - Treasure Island, FL 33706
Excellent service and pricing from start to finish.
Steve - Treasure Island, FL 33706
Ordered a standard service for a system functioning properly and under warranty Tech arrived and found a “bad capacitor”. Stated it required repair and charged hundreds of dollars for the service. Shortly after departure, system started operating inefficiently Next day the system was unable to maintain cool temps during peak usage Called again. They sent out another team who tried to convince me this was coincidental and likely due to the storms. They were unable to complete repairs and said it would likely be between $1500-3500 to fix and would be able to get back on Monday when the parts center was open There were some red flags to me. I called another company for a second opinion. The tech showed up and nothin minutes found the issue. The original tech installed the wrong capacitor and it was damaging my system. Repairs were made and it is now functioning properly. Definitely suspicious
Davidson - Treasure Island, FL 33706
Jason said y’all don’t provide filters when doing semiannual scheduled service. That is unbelievably petty.
Consistent quality service
Davidson - Treasure Island, FL 33706
Jason came when needed and was comprehensive in determining what was wrong with our hvac. I have confidence Total Air will keep our systems running. Thank you.
GS - Treasure Island, FL 33706
Excellent service by Total Air techs! Professional and knowledgeable. Thanks for a job well done!
On time appointment
Morse - Treasure Island, FL 33706
Good service, on time, actually early, advance notice of arrival appreciated.
Timely and friendly
Burroughs - Treasure Island, FL 33706
Nevin has helped us a few times. He is always on time, super-polite and explains everything well.
Very good, thanks
Stoye - Treasure Island, FL 33706
Hewson - Treasure Island, FL 33706
Sergey was terrific. He fixed the drain and was very pleasant to me. A/c System is working fine now
Excellent preventive maintenance!
Roy - Treasure Island, FL 33706
Diagnosed a bad capacitor and replaced it. This a avoided the AC breaking down when cooling becomes important in a few months. Excellent professional services provided by Total Air Inc and their technician. I highly recommend them.
Arrived at customers house for system not working. On arrival. Customer showed me to air handler unit. Looked underneath and saw ice. Noticed unit is a heat pump. Turned in heat mode to defrost. Once unit had no ice turned to cool mode. Hooked up gauges. Pressures and readings were not showing signs of low Freon by showing signs of Bad airflow. Went inside and fan was not blowing hard. Made sure settings were correct and settings were correct as far as speed. Changed the tap around to make sure speed setting is working and speed. Setting is not working. Through all three speeds on all three modes unit stayed a consistent, very slow speed. Call customer and inform them of this. Suggested we get a new fan for this unit. We will look for price and availability and get back to customer when motor is found. Collected payment and signature in left. Thank you for choosing total air!
Called out today due to no cooling. Upon arrival client stated that the system finally reached 77 degrees but continuously runs. Inspected evaporator coil and noticed what appears to be an oil spot. Measured the temperature drop across the coil. Went to the roof and checked refrigerant pressures. The system is low on refrigerant. Explained the clients that if the system is low on charge that means that it is leaking from some point. Gave options for a one time fill, leak search and a worst case scenario. The machine is 10 years old and out of manufacture warranty. Due to the cost of potential repairs and age… they would like to see what options they have for replacement. I left the machine in the same condition as arrival. Thank you for always choosing Total Air!
Called out today to take a look at ductwork and mold growth. Client was unfortunately hit with flood water. Return plenum is soaked with water. Metal ducts are ran throughout the basement with insulation falling off. The bedroom at the top of the stairs lacks airflow. (Conjoined with daughters room) Kitchen vent is ran through cabinets which also has poor airflow. Client mentions that sunroom has no ventilation and wondered if we can run extra ducts to that room. I explained that the machine only produces a certain amount of cooling capacity. By running more ducts it will take away from other areas of the home. Best solution would be to install a mini split unit to control that room. Spoke with the client about our preventative maintenance plan and the difference between our pure air (three year bulb, lifetime warranty) vs our economy uv light (12 month bulb) The drain line is rain inside the house and is draining into the foundation.. I will send a comfort advisor out to give
Called out today to perform a full system leak search. Had multiple hits in the evaporator coil with the electronic leak detector. I noticed that the bulb if the txv was not strapped down causing vibration. Brought this to the customers attention and recommended replacing that as well. Searched all joints and condenser coil. Office will call with a final price and timeline for repair. Thank you for always choosing Total Air!
Called out today due to no cooling. Client stated that her system continuously runs. Checked all electronics and motor components to ensure equipment is operating properly within manufacture specifications. Checked filter. Drain line was not backed up. Checked refrigerant pressures and found the system extremely low. Gave options for preventative maintenance, leak search and refilling the system. Added three pounds of 410A. Monitored pressures and temperatures. Will return tomorrow from 12-2 for a leak search. Enrolled in preventative maintenance agreement and applied 100$ off coupon. System is running. Explained to the clients that the house will drop in temperature at about a degree an hour. Thank you for always choosing Total Air!
Under warranty removed fan and installed new fan
Upon arrival customer told me AC was blowing warm air. Went to the condenser the fan was running and the compressor is running. Turned off power and I checked the capacitor just to make sure the capacitor was reading where it should and it was good. Put gauges on a system and it is almost empty of R 22 Freon. System will need to be replaced.
Return to customers home to perform court at work. Went on a roof pulled the old disconnect off and installed a new disconnect and whip to the condenser. Installed a surge protector. Insulate it the suction line with a UV insulation. Did a low-voltage repair because it was falling apart on the roof. Cut the old thermostat wire out and replaced up to 15 foot of thermostat wire on roof to condenser. Went to the condo where the air handler was and installed a pure air X. Restored AC to home
I was initially able to make contact with customer upon arrival and gave me access inside of the condo unit. However, I needed to gain access to the rooftop and the door to the rooftop was locked. I attempted to call the customer on three occasions, but did not get any answer when the customer calls back, please inform her that she would need to reschedule at a time when we have access to all pieces of equipment and also, we must be able to contact her at any given time during the service call. The service call is unable to be completed at this time.
Upon putting arrival customer told me the unit was leaking water on the floor. The unit is a PTAC threw the wall. Went outside and found the drain disconnected I put the drain back. Also the grout on the patio is all cracked up. Could be leaking from the rain coming in on the patio.
upon arrival customer showed me AC unit in garage that she was concerned of bacteria building on the outside of the ductwork. The reason why bacteria is building up on the ductwork is because it’s hot in the garage and cold in the ductwork. There is no active activity of bacteria in the air handler or blower motor. I wiped off as much as I can on the ductwork. I recommend installing a pure air X, Oxidizor and a EAC 24x36x1. Customer agreed and it is on order. When we come back I mentioned to customer I will wipe it down again and put mastic over it. Will call when the material is in to schedule. Put an estimate together for a new wall mount return grill. It is a special return grill so please call if you want to move forward with It. will take 4 to 6 weeks to come in. When it is approved from customer. Please call customer to schedule an appointments for comfort advisor to come out to give estimate on new duct work.
Returned to replace warranty TXV. Adjusted refrigerant level from what was lost. 1lb.
Called out to inspect water leak. There is drywall damage above one of the supply air vents. I removed the supply grille and inspected. I found the insulation to be dry and no obvious signs of water coming from the hvac system. I assume the water is coming from above. The office manager is going to have the above unit inspected to see if they can locate water damage. If there is no signs of water leaking in the above unit we will have to return and cut a 10”x10” hole in the ceiling to access this subfloor to observe the damage. *The office will have to create an estimate to cut a hole in the ceiling. This will need 2 guys. I informed the customers that the drywall repair would be on them as we do not do drywall. If the customers call back and accept the quote we will not charge another service fee. All photos and videos are uploaded.
8/9/23 Arrived to the PM, C/U is on the roof. 3 story’s high, photo uploaded to ST. Will need to reschedule and 2 person job. 8/14/23 Upon arrival to the scheduled system maintenance, I was shown to the a/h in the main floor closet and c/u on roof. I pulled off the panel door to inspect all electrical components connections, collect amp draw/voltage readings off electrical equipment, and check the unit for cleanliness. The a/h unit is free of biological growth. I recommend a UV light system to keep the unit clean and produce better indoor air quality. The evaporator coil and blower fan are clean. An electronic air cleaner will also replace the standard filter. I spoke with the customer and told her that 1 filter is good for the a/h and the 2nd is not necessary. The d/t temperature was 20° and within normal range. Photos uploaded to ST. All electrical components were secure and within factory range. I then vacuumed the condensate drain line to remove and blockage or debris. I ensur
Complete no cool call. Customer states the system is struggling to keep up. I did a full inspection of the system. I found the indoor blower motor to be failed. The motor is only running at 5% capacity. While the system is running the fan is not pulling enough hot air over the evaporator coil causing it to freeze. The indoor blower motor will have to be replaced. I confirmed warranty and left an estimate for the repair. Customer requested that I send her the invoice and she will call back when she’s ready. I informed our customer of the prime maintenance membership and left an estimate for this as well. Thank you for choosing Total Air!
Upon arrival to the scheduled system maintenance, I was shown to the a/h and c/u on the balcony. I pulled off the panel door to inspect all electrical components connections, collect amp draw/voltage readings off electrical equipment, and check the unit for cleanliness. The a/h unit had minimal biological growth. It has a UV light system to keep the unit clean however it is due for a new bulb. The evaporator coil and blower fan are clean. The d/t temperature was within normal range. All electrical components were secure. The blower fan mini capacitor in the a/h is low and ready for replacement. The homeowner will not move forward at this time. This is a common drain line. I added vinegar provided by the customer and flushed it with water. I then replaced the filter provided by the customer. I also suggest an electronic air cleaner. This filter uses static to pull in particles and help prevent debris build up. The c/u system refrigerant charge is within normal range and all electr
Terror existing air handler and coffin box replace new coffin box tie into existing metal, return tie into existing Plenum new heat show mechanically fasten to unit flush copper line, set flush drain line, hook up copper hook up drain line, low-voltage and high-voltage mastic. All seams share out old condenser replace padlock pad Thai down to one condenser tied down four corners on top hook up copper high-voltage low-voltage nitrogen test copper 400 psi for 30 minutes vacuum to 500 µm start up. Everything is calling to factory specs job is complete pictures taken.
Secondary pan was filled with water and tripped the water overflow safety device. I flushed out drain system and emptied water out a secondary pan. I recommend it to customer to have us to do a maintenance as that would’ve prevented the failure from occurring. The customer is leaving to go out of town today and said he will be gone for 6 to 7 months and stated that he will address and maintenance plan at that time.
Customer had a touchscreen thermostat. That was non-responsive. I changed our thermostat for a programmable T6 thermostat in which the customer wants something more simple.
Upon arrival customer said AC was not cooling properly. The indoor fan motor came on the outdoor came on but not blowing cool air put my gauges on and found it low in Freon in the compressor is over ramping. The compressors amp in at 32.3 Amps. added 2 pounds of 410 A to system to get the customer cooling
Upon arrival customer charged me through the wall condenser in closet and air handler and addict I need a tuneup. Went to the condenser checked all amps and volts and the compressor is reading 47.1 Amps. The compressor is over camping and his hot to the touch. Contactor is pitting and capacitor is below factory specs. Recommend replacement customer denied. went to the air handler checked all amps and volts on motor. The evap coil is rusted bad. Talked to customer about having a comfort advisor out and he agreed. 8/2/23
Arrived at customers house for no cool. On arrival. Found customer with a clogged drain line. Informed customer float switch was activated. Suggest we vacuumed out and flush drain line. Customer agreed. That you don’t flush drain line. Heard good vacuum upstairs. Unit now running fine. Talked to customer about taps membership and customer decided to sign up. Collected payment and signature and left. Thank you for choosing total air!
Upon arrival indoor unit was blowing but outdoor unit was off. Found bad 35+5 capacitor and replaced with warranty part after confirming with homeowner that we are allowed to do so. System is on and cooling took pictures of pressures
Called out today due to no cooling. Upon arrival the system was tripped due to the float switch tripped. Float switch had vinegar located inside. Took drain apart and it was completely clean. This is a common drain on the 3rd floor and she stated that maintenance hasn’t cleared it lately. Offered drain solve but there is no guarantee for back ups due to the common drain. Removed vinegar from emergency port and tested all electronics and motor components to ensure equipment is operating properly within manufacture specifications. Checked filter. Added hot water to drain line to ensure proper drainage. Drains well to where I can see before entering the wall. Checked refrigerant pressures. Equipment is operating properly at this time. Thank you for always choosing Total Air!
HVAC Repair. Customer expressed concerns about the sound. The compressor makes when shutting off. I did a complete evaluation of the system and cycled through multiple cycles to replicate the noise. I did hear the noise in which the customer was speaking of, but it was very intermittently in producing the sound. The system was running at a design 8 to 9° circle with a 18° superheat and a 17 to 18° temperature split so therefore with those measurements the system was running well. I attempted to add a hard start to see if that would help to lessen the sound on start up and shut off and it did not . So my recommendation to the customer was to replace the compressor under warranty to illuminate the problem altogether as the problem will only get worse over time. The customer declined to replace the compressor as she is in the process of selling the residence which has been on the market now for two months.