AC Repair For Tampa, FL, Area Homes
Without a trusted local air conditioning service provider, it would be very uncomfortable throughout Tampa's scorching summers. Thanks to Total Air Inc., you will be comfortable all year long by ensuring that your cooling system operates at its best. With decades of experience serving Tampa, FL, you can be sure that our professionals are doing something right. Our commitment to staying current with emerging technology and our top-notch customer support are what enable us to remain in business.
We invite you to read some of our reviews from others in the Tampa community. Connect with our team today for fast reliable service!
Air Conditioning and Furnace Installations, Maintenance and Service
As your local neighborhood air conditioning service provider, Total Air focuses on maintaining your system in peak condition so you can stay at a comfortable temperature regardless of the weather outside. Our team will perform a thorough diagnosis of your unit, ensuring your AC works well all year long! We are happy to serve the entire Tampa area, including Westshore, South Tampa and Hyde Park.
We will identify any issues we see as well. We then will offer the best solution to quickly get your house comfortable again.
Your AC system needs our maintenance services to continue operating at its best. The majority of the time, when you least expect it, a unit will break down, leaving you in need of emergency work. You may arrange routine maintenance visits with qualified professionals to check your system and make sure any minor issues will be taken care of in order to avoid dealing with this type of unpleasant situation!
Our professional team also provides expert AC installation services when it's time to replace your older system. Connect with us today for an estimate on a new home air conditioner!
for Tampa, FL
No Heat- Corrected
Swengros - Tampa, FL 33647
Response from Total Air, Inc.:
Your kind words about our heating and cooling service mean a lot to us. Thanks for leaving such a positive review!
Quick and complete
2 Roof Units replaced - Tampa, FL 33616
We got our 2 A/C Units replace in one day. That is a spectacular feat. They took our old ugly dirty units air handler and roof top compressor units and put in 2 new beautiful units quickly. They were very organized and came on time and even were finished early. They organized a crane company to show up when they needed to hoist the new units up and remove the old off the roof. They also put carpet and hardwood protection down so there was not harm or dirty floors left behind. Very satisfied and it was money well spent.
Melissa - Tampa, FL 33615
First of all the office staff is a breath of Total FRESH Air”…lol. No, but seriously they were calling to update me on the time the tech would arrive & they were SO nice! Then the tech came & thoroughly checked everything. He explained everything along the way & left me with tips on how to keep up my AC unit. The presentation was very excellent.
Tony - Tampa, FL 33609
Performed annual AC tune-up on system for homeowner in Westshore. Cleaned unit, tightened connections, ran diagnostic checks. System is working well. Replaced thermostat battery. Air conditioning should perform well all summer.
Performed AC maintenance service for homeowner living near Drew Park in Westshore. Cleaned out unit, gave it thorough inspection, lubricated moving parts, checked thermostat. Unit had a few loose connections which I tightened. Air conditioning system should function more energy efficiently and perform better throughout summer.
Called out today due to no cooling. Upon arrival air handler was running but the condenser was not. Found that the contactor was not allowing power to pass through. Replaced contactor and tested all electronics and motor components. Checked refrigerant pressures. Measured the temperature drop across the coil. Gave options for maintenance agreements and repairs. Equipment is now operating properly. Thank you for always choosing Total Air!
Called out today to perform a precision tune up. Checked all electronics and motor components to ensure equipment is operating properly within manufacture specifications. Checked filter and cleared drain line. There was water sitting in the drain line and pan. I recommended a drain treatment using drain solve. Also advised clients to add vinegar and hot water to the drain lines once a month to help prevent obstruction. Measured the temperature drop across the coil. The UV light is becoming dull and burned. Typically have a life span of about 1 year. Outside I removed the fan from the condenser and cleaned the coil from the inside out. Vacuumed drain line clear from outside port. Client approved drain treatment and UV bulb replacement. Equipment is operating properly at this time. Thank you for always choosing Total Air!
Called out today to perform a precision tune up. Checked all electronics and motor components to ensure equipment is operating properly within manufacture specifications. Replaced client provided filter and cleared clogged drain line. Client stated that a lot of renovation has been going on within the home. The blower wheel and coil and covered in dust and debris. We were going to pull and clean the blower wheel today but I recommended having it cleaned when the work is finished. Measured the temperature drop across the coil. Outside I removed the fan from the condenser and cleaned the coil from the inside out. Vacuumed drain line while pouring hot water. Recommended a drain solve treatment to help remove blockage. This is the last visit on this years maintenance agreement Renewed preventative maintenance plan and treated drains with drain solve. Equipment is operating properly at this time. Thank you for always choosing Total Air!
Customer complaint heat not working Upon arrival located air handler in garage and condenser onside of garage During inspection found system having an error code of hpc lockout. Inspected and tightened electrical. Gained access to installer options and cleared the fault code. Checked filter found filter plugged which was starving the unit of air which tripped the error code of hpc lockout. Cleared error code. Replaced dirty filter. Calibrated and tested thermostat. Cycled heating. Checked refrigerant levels. Took temperature difference. Cycled cooling. Checked refrigerant levels. Took temperature difference. System operating to factory standard
Called out today to perform a precision tune up. Checked all electronics and motor components to ensure equipment is operating within manufacture specifications. Replaced client provided filter. Flushed drain lines and vacuumed clear from outside port. Drain line was heavily clogged with debris, I recommended treating the drains with drain solve. Measured the temperature drop across the coil. Outside I removed the fan from the condenser and cleaned the coil from the inside out. Found a wire rub out from the compressor. Added electrical tape to create barrier. Clients maintenance agreement is good until 2024. Will order EAC filters. Cleared drain line with drain solve. Equipment is operating properly at this time. Thank you for always choosing Total Air!
Customer concerned about unit not cooling properly. Checked blower motor operation and inspected evaporator coil condition. Checked safety float switch and inspected drain line. Located sensor on emergency drain pan not reset. Reset the safety float switch and inspected drain line. Unit is now cooling properly. Recommend new safety surge protector on outside condenser unit to prevent voltage spikes and electrical failure. Customer unit under warranty.
Called out today to perform a precision tune up on four units. Checked all electronics and motor components to ensure equipment is operating within manufacture specifications. Checked and replaced all filters and cleared drain lines. Measured the temperature drop and rise across the coils. The farthest unit in the air handler emergency drain pan is completely rusted out. Made client aware of its condition and the fact that it could deep through onto the ceiling. The guest house UV bulb is out and the coil is rusting and condensation into the drain line. Outside I removed the fans from the condensers and cleaned the coils. I noticed that the contactors were heavily pitted outside. Armaflex is rotted and falling off of both carrier condenser units. Replaced three contactors, Armaflex, and renewed maintenance agreement. Equipment is operating properly at this time. Thank you for always choosing Total Air
Called out today due to no cooling. Tenants told me that this has been going on for about a week now. Upon arrival float switch was tripped due to the ice thawing. Left system off with the fan on to help the ice melt. The filter was extremely dirty and the ice was stuck to it. I was unable to see the under side of the evaporator coil. Thank you for always choosing Total Air! Wade h 11/10/2022 Unit has thawed out. Checked thermostat calibration and filter location. Filter is very dirty and needs to replaced. 18x18x1 Highly recommended pull and clean the evaporator coil. The coil is extremely dirty and can not breathe properly. Unit will freeze up when coil is not cleaned and can not pass air. I have sent this customer recommended estimate for membership and pull and clean evaporator coil. Needs Customer approval for evaporator cleaning.
Replaced blower motor and wheel. Tested system operation. Equipment is operating properly at this time. Thank you for always choosing Total Air!
Upon arrival customer showed me a water stain on the sheet rock in the garage. I went up in the attic and there is no drain or or water in that area. I want to say it is coming from the roof.
No cool. Downstairs unit drain line backed up. Drain lines are all built up with debris. I cleared the drain with pressure at no charge today. Home owner authorized drain solve treatment on all four main house drains. Due to weather and lack of supplies this will have to be scheduled next week. Home owner wants to purchase 4 oxidizers to add to her existing pure air system. I do not have a stand alone task for this so we will have to give estimate Tuesday morning. System cooling at this time.
Tune up/ check system. 3 ton unit less then 2 years old. Not keeping temperature and will not reach set point during the day. System has multiple issues 1. Return duct is undersized and causing unit to sweat heavily. The previous company tried to add a second return grill and duct in line with the original return. This has a highly diminished effect on the amount of the the system is pulling. This needs to be corrected to allow system to breath properly and stop sweating. 2. Split temp (delta) at airhandler plenum is 16 degrees. While this is lower then the desired split, this should be enough to satisfy the temperature. When reading Temps at the registers, the air has gained 4 to 5 degrees and now has a delta of 12. This will not reach a set point of 72 in the home. The supply duct work is picking up heat load before being delivered to the living space. Supply Ductwork should be replaced. 3 pressures seem marginally low for a Rheem system. Due to the air flow issues, this may
Called out today to perform a precision tune up. Checked all indoor and outdoor electronics and motor components to ensure equipment is operating within manufacture specifications. Checked filter and cleared drain line. The coil is heavily impacted with biological growth. It’s coating the wires, blower wheel and casing. I highly recommend cleaning or permanently eliminate growth by UV sterilization. Outside I ensured the community drain was free of blockage. On the condenser I noticed that the contactor coil is becoming pitted as shown in video. The bottom of the condenser coil is extremely corroded as well as the shell of the compressor. Client choose to get a one time cleaning of the blower wheel and the evaporator coil in place. Also replaced contactor. Equipment is operating properly at this time. Thank you for always choosing Total Air! Clean and go
Terror out existing rooftop condenser fly off with crane flying new one with crane I brought it up fly 70 gallons of roof paint to the top of roof with crane hair out air handler on stand coffin box replace call tin box replace air handler Cayenne high voltage low voltage drain line copper Thai in coffin box put in new surge protector at disconnect on roof will need to return to put in Elite light on both units nitrogen test 400 PSI vacuum down to 500 Micron start up everything working in perfect condition
Customer concerned about unit not cooling properly. Checked breaker and safety float switch and inspected drain line. Checked thermostat calibration and filter location. Customer replaced filter. Unit is cooling well and drains at this time. Customer approved for 1/2 preventative maintenance visit and (2) uv bulb replacement Performed preventative maintenance tune up. Checked blower motor operation and inspected evaporator coil condition. Checked safety float switch and inspected drain line. Cleaned vacuumed drain pan and drain line. Checked thermostat calibration and filter location. Customer replaced filter at this time. Checked condenser operation and rinse condenser coil. Checked refrigerant levels and check test start up components. Replace (2) 24 volt uv light stick probe to prevent biological growth in air handler and evaporator coil.
Customer concerned about unit not cooling properly. Thermostat given error code. Checked thermostat calibration and filter location. Checked thermostat wiring and air handler control board. Checked low voltage wiring in condenser. Unit installed by another company. Customer is not satisfied with that company. Bad low voltage wiring, needs to be replaced with 18/4 stranded wire that is designed for communication and plenum rated. Follow up to be replaced and repaired. Needs 50â€™ communication wire and 2-3hrs. Also discuss new membership and units to be performed preventative maintenance. 2/18/2022. Replace old thermostat wire with new 4/18 stranded communication wire. Termite all connections and checked operation. Set up WiFi for customer and checked unit operation. Unit setup and cooling at this time.
Completed maintenance on a heat pump split system. Checked all electrical components for proper volts and amp draw. All components are within factory spec. Dual capacitor tested ok. Heat kit tested ok. Changed supplied filter. Split temp above 19 degrees. Found biogrowth in airhandler. Cleaned and sanitized airhandler cabinet. Pulled blower assembly and treated. Installed a pure x uvc light system with life time equipment warranty. The pure x has a 3 year bulb life. Re assembled and tested . System clean and operating normally at this time.
Installed filter rack and EAC system. Sealed plenum and rack. Tested EAC system. System working properly. Left box of filter media on air Handler for easy replacement.
Performed preventative maintenance on the system. Cleaned drain, checked filter, cleaned return grille, checked coils, tested/inspected electrical components, checked refrigerant pressures, tested reversing valve operation, and tested operation of the system as a whole in both heating and cooling modes. I found that the run capacitor in the condenser was weak. Customer gave approval to change this out. He also has signed up for the TAPS Annual Membership. I ensure the system was operating after repairs. This system has 8 degrees subcool with a 19 degree TD.
Maintenance 1 Performed maintenance on a Rheem heat pump split system. Checked all electrical components for proper volts and amp draw. All components are within factory spec. System refrigerant pressures are at the correct levels. Cleared the drain line. Home owner signed up for our maintenance plan. He also requested a UV system. I installed a pure x iv system. He would also like a EAC filter system installed. For EAC filter install, we will need a filter rack from Rheem. The rack will need to be installed between the return and return plenum of the air Handler. Office will contact home owner with a quote for this. Home owner would also like a quote on a mini split addition. Corey is scheduled for a visit between 10 and 12 tomorrow. System operating great at this time.
Arrived at customers house for system inspection. On arrival customer show me to to Erin Angel is. Started on air handler on the second floor. Air handler was putting out proper delta-t. Had a bit of covering on the underside. Install put filter on rack instead of on unit. Suggested customer get an electronic filter for the proper filter place. All electric wiring was secured. Next went to upstairs air handler. Inspected evaporator coil and saw some bio growth beginning to form. Fan in electrical cabinet were clean. Unit was putting out proper delta-t. Next one to condenser units. Both units pressures and readings were of acceptable range. Both units contractors were putting out proper voltage. Capacitors with an acceptable range. All units check out. Gave report to customer and customer was please. Collected payments and signature and left. Customer happy.
No cool: On arrival, I found capacitor and headstart inoperable. Common high volt wire was burnt off as well. Replaced contactor and rebuilt wiring. System now cooling normally.
Found not cooling due to clogged drain line. Cleared with high pressure nitrogen. Primed drain. Checked operation. System cooling and draining properly at this time.