Check Out Our Work in Redington Shores, FL
Total Air provides air conditioning, heating, water heater and plumbing services to the residents of Redington Shores, FL and the surrounding areas. Read our reviews and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Redington Shores, FL.
for Redington Shores, FL
Best A/C company in Pinellas County
Steinke - Redington Shores, FL 33708
The entire team at Total Air communicates with their customers every step of the process, from initial contact through job completion, while delivering clean and thorough work.
No heat/cool<br> <br> Hydro thermal heat pump system not running compressor. Found bad con control board not releasing y to contactor. I bypassed board for temporary operation. Board will need to be replaced. <br> <br> Found pure x uvc bulb burned out. Home owner approved replacement of bulb. <br> Set transformer to 208v for the correct incoming line voltage. <br> Home owner signed up for maintenance program today. First maintenance should be scheduled after repair is completed. <br> <br> Office to check warranty and part availability. Office to contact homeowner with repair quote. <br> <br> System operating at this time. <br> <br> Model sv0411vtcfrtpddxatxxxxxx7xxxx1xxxxsba<br> <br> Serial. 29400740000027735071982
Complete member tune up. Customer is concerned about some biological growth that is forming around only (2) supply vents downstairs. I found that there is a gap between the ceiling and the grille causing our issue. The ducts and inside of the grille are clean. I caulked the edges of the grille to close the gap and ensure proper airflow on both vents. Inspect and change customer supplied filters. Clear all drain lines with vacuum. Central Air System (1): Inspect electrical components. Test amps and volts. Delta t measures at 20 degrees. Ensure system is running properly in all modes. A picture of the evaporator coil will be uploaded. There is no biological growth inside of this air handler. The UV device is functioning properly. All safety switches are functioning properly. At condenser checked pressures, temps, amps and volts. Left system in good working order. Central Air System (2): Inspect electrical components. Test amps and volts. Delta t measures at 19 degrees. Ensure system i
unit #1 Customer showed me a ac unit in the closet that was not working. 8t is old. Turned thermostat on and indoor fan came on but not the condenser. Found the compressor out on LRA. This unit has to be replaced. Pulled disconnect. Unit #2 Customer told me this unit is old and does not seem to work right. I turned unit on and both air handler and condenser came on with a 18 degree split. This one is old they want a price to replace this one also. Unit #3 This unit is new and there is nothing wrong with this unit Corey scheduled Monday 1/3/21 between 12 and 2 to give customer an estimate.
Replaced mini split mount with full welded aluminum mount, replaced Mitsubishi mini split condensing unit. Nitrogen tested, pulled system to 500 microns. Verified system was cycling properly. Customer is satisfied at this time.
Unit not cooling due to a pressure sensor error. Reset both boards error went away. Just a miscommunication error on the two communicating boards. System running properly at this time.
System is critically under charged discussed options with client fortunately technician did not have leak stuff left on truck. Technician recommended replacement client agreed office to contact clients to arrange meeting with Corey.
The 2005 air handler and 2014 heat pump is completely out of R22 Refrigerant recommend system replacement. Corey is scheduled for today 3-5pm arrival.
Cycled and inspected equipment. Found equipment from 2005 with some wear and tear. System is operational at this time. Left system in good working order for now. I informed customer about equipment and estimate. Customer stated he would like to move forward with getting a estimate to replace but it will have to wait until he receives ownership of property. Recommend: new equipment due to age and overall condition of equipment. Also installing a new pure air x whole house germicidal unit to eliminate and prevent bio growth.
Performed routine maintenance on 3 total systems checked pressures amps volts coils drains temps all systems are running to manufacture specs at this time
Cycled and inspected equipment. Found thermostat locked. Unlocked thermostat and went over step by step to ensure customer was informed on how to unlock thermostat. Left system in good working order.
Cycled and inspected equipment. Found system with a blown 5 amp fuse. Found low voltage wiring in poor condition causing shorts. Also found contactor pitted. Repaired wiring and short. Installed a new contactor. Left system in good working order for now. Scheduled Corey same time as tune up to avoid multiple appointments per customers request Thursday 8-10 a.m. Recommend: highly recommend replacing system due to cost of future repairs, age, and overall condition of equipment.
Completed the tune up. System are working properly. Talk to the customer about membership. She will think about it.