Air Conditioning Repair and Services Near Palm Harbor, FL
At Total Air Inc., we have been proudly serving the Palm Harbor area since 2003. We are a veteran-owned company that provides expert service and quick, reliable AC repair. We offer full furnace and air conditioning services for your home. We are fully licensed and insured and our techs are highly trained and experienced. The main goal of our HVAC company is to keep customers cool and comfortable. We are available 24/7 for any heating and air emergencies, and our pricing is upfront and fair for the quality of work we provide. We offer a 100% satisfaction guarantee on all of our work, so you can be sure you're making the best decision for your home.
Our residential and commercial HVAC services include:
- Air Conditioning Repairs
- Air Conditioning Installations
- Heating Repairs
- Heating System Installations
- And More!
Contact us today at (727) 822-7700 to schedule a consultation!
Palm Harbor, FL Air Conditioning System FAQs
You can expect to pay between $100 and $150 for annual AC maintenance. Cleaning and tune-up costs roughly $125 for the average household, which includes checking, tightening and testing all parts, as well as minor part replacements such as air filters and cleaning coils.
To a large extent, the price of your AC installation will be determined by the system you select. You can expect your central air conditioning system to cost anywhere from $3,800 to $7,500. If at all feasible, have the AC installation done in the spring or fall. You may spend less on installation and the contractor may do the job faster if you schedule the installation during the off-season.
Here are the top three ways to improve your indoor quality:
- Open Your Windows
This brings fresh outside air into the home and removes allergens and other hazardous compounds in the environment.
- Use Air Purifiers
Using an air purifier regularly is a must for properly cleaning your home air. They are made to remove impurities from the air environment while also leaving it clean and healthy.
- Maintain A Humidity Level of 30 to 50%
You will reduce the prevalence of dust mites and mold development by using a dehumidifier. Molds create mycotoxins and allergens, which can be harmful to your health.
for Palm Harbor, FL
Our Reviews by City
Great service and professional
Baker - Palm Harbor, FL 34684
Great service, fast, informative
Bridges - Palm Harbor, FL 34684
David - Palm Harbor, FL 34684
Baker - Palm Harbor, FL 34684
Professional and hard workers
Very polite and professional, good service
Baker - Palm Harbor, FL 34684
Very professional and polite
Upon arrival customer told me unit was not cooling the house. I found the breaker shut off on the air handler in the condenser. I turned them on and unit turned on. Then I realize the compressor was not running. I found a bad turbo 200 X. Replace the turbo 200 X And restored AC to home. It was under warranty.
Came out to do maintenance. Checked pressures and found system to be a little low. Checked amp draw and capacitance. After discussing with homeowner, added pound of refrigerant back into system. Checked TD and amp draw on indoor fan motor. Also visually inspected evaporator coil and primary pan. Treated and flushed condensate line. Made a suggestion for indoor air quality with an air purifier and sent estimate. System is cooling and functioning properly at this time
Refrigerant repair. Refrigerator repair was completed. No further leaks were detected within the system. Customer will be calling in on tomorrow to add the additional system to the maintenance agreement and to schedule a maintenance tuneup for both systems at the same time.
I system was a little low on refrigerant. I recharge the system with 3 pounds of refrigerant. Please call customer tomorrow to set up a follow up call to do a full inspection of the system for Monday or Tuesday.
Complete no cool call. I did a full inspection of the hvac system. I found the system to be low on refrigerant. I offered the full system leak search to pinpoint where the leak is coming from to make the repair. I also added (3) lbs of 410a to get the customer cooling until repairs can be made. I cycled and inspected the equipment ensuring proper operation. The system is now cooling to manufactures specification. Our customer will call us if he decides to move forward on the leak search. Thank you for choosing Total Air!
Tear out air handler and hanging kit replace new hanging kit new air handler new drain pan attached to hanging kit hook up existing plenums drain line after flushing copper after flushing, high voltage and low voltage flow switches and line and pan. Change new thermostat tear out old condenser replace new condenser on new pad, tiedown four corners Tyanne copper after the flush nitrogen test copper 400 psi vacuum down to 500 µm hook up high-voltage low-voltage and drain line start up everything running factory, specs, checking and cool and heat mode
Called out today due to no cooling. Upon arrival system was intermittently running. Inspected air handler and noticed the drain line was heavily impacted. Checked all electronics and motor components to ensure equipment is operating properly within manufacture specifications. I found that the capacitor has failed. Fan motor is hot to the touch and pulling maximum amperage. Checked refrigerant pressures. Equipment is 17 years old and well out of warranty. Gave options for repairs vs replacement. Client is aware of the wait time for the motor. Equipment is running at this time but they are aware that it will fail again. A comfort advisor will be out within the hour to give options on machine replacement. Enrolled in maintenance agreement for both units and waived trip charge. Thank you for always choosing Total Air!
Arrived at customers house for system inspection. On arrival customer showed me to air handler unit in garage closet. Unit is equipped with a pure air UV defense system. Bulb is almost to suggested change date. Showed to customer and suggested we change today. Customer agreed. Changed out bulb and unit is now running fine. No water is seen overflow reservoir. Float switch currently working. Unit is creating proper Delta t. Next went outside to condenser. Opened electric cabinet and all wiring was secured. tested components. Contactor sending proper voltage. Capacitor within acceptable range. Unit is not currently equipped with a surge protector. Vacuumed out condensate line and heard good. Vacuum at air handler unit. Next looked at Ductless split unit. Unit was producing proper delta. T. Went through remote control and showed customer different settings. Rinsed off ductless split filters. Coils were clean. Fan wheel was clean. Unit was producing proper delta. T. Outside condenser c
Complete no heating call. After inspection I found the thermostat to be failed not sending the proper signals. I jumped the system out to ensure all parts and components are working properly as well as heating and cooling modes. The customer will buy and install his own thermostat as he wants to go back with a nest and initially installed the first one. Customer is now a prime maintenance member. *See Notes*
Arrived at customer's house for 3 unit system inspection. On arrival customer showed me to air handler units. Started with air handler in laundry closet. Air handler was equipped with UV light. UV light is within dropper date. Inside cabinet is clean. Under evaporator coil is clean. Unit is producing proper Delta T periodrain safety is currently working. Next went to 2 air handlers and upstairs. Checked under both evaporator coils and under both evaporator coils were clean. Both units are equipped with UV lights that have bulbs in acceptable date. Open both air handler cabinets and blower wheels were clean. Tops of evaporator coils were clean. Both units were producing proper Delta T. Both units drained safeties were currently working. Next went outside to condensers. No condensers are equipped with surge protectors. With these units being by water and risen on a porch they are More prone to lightning strikes And electric surges. 2 units are inverters, and one is a standard unit
Arrived at Home for system not cooling. On arrival fan was running in air handler. Went out to condenser and nothing was running. Tested capacitor and capacitor was bad. Suggested customer change and customer agreed. Changed capacitor and system now running fine. Suggested a surge protector to prevent this from happening again and customer agreed. Installed surge protector and unit now running fine. Gave report to customers and customers happy. Suggested customer sign up with taps plan and customer agreed. Collected payment and signatures and left.
Tear out air handler drain pan hanging kit install new hanging kit new air handler new drain pan tie an existing copper high voltage low voltage tear out existing condenser and Pad new pad leveled new condenser on new pad thai down four corners tie an existing copper high voltage low voltage nitrogen test 400 PSI vacuum down to 500 micron install new thermostat install 2:30 amp Breakers start up everything working in perfect condition added 2 lb 3 oz 410A refrigerant customer is happy and Cooling job complete one check and the rest paid on card damn so they
Maintenance 1 Completed maintenance on a strait cool split system. Checked all electrical components for proper volts and amp draw. All components are within factory spec. Heat and cool working properly. Vaccuumed drain line. Found ptrap broken and laying on the ground at the co condensate drain exit. Rebuilt so drain will flow properly. Found wiring splice at the condenser heavily damaged and without insulation. Re wired from splice to the condenser. Found airhandler with heavy bio growth in the airhandler blower compartment. Discussed sanitizing and UV options with home owner. She declined at this time. An estimate will be.attached to this invoice. System operating normally at this time.
Maintenance Checked all electrical components for proper volts and amp draw. All components are within factory spec. Corrected loose common wire connection. Dual run capacitor tested 42.3 of required 45. This is still considered good. Cleared drain line. Changed out EAC filter for the homeowner. System pressures are at the correct levels. Cooling temps are normal. Replaced pure x uvc bulb that expires this month. Homeowner renewed maintenance membership today. System operating normally at this time.
No cool Found low voltage short caused by contactor. Replace the low voltage fuse and contactor. Tested system. System now cooling properly Homeowner signed up for maintenance program today.
Completed maintenance on a heat pump split system. Checked all electrical components for proper volts and amp draw. All components are within factory spec. Back up heat tested ok. Cleared drain line. Found weak capacitor reading 20/1 of required 45/5. Replaced with a t200 cap with 5 year warranty. Found biogrowth in airhandler. Cleaned and sanitized the airhandler. Installed pure x uvc light system with lifetime equipment warranty and 3 year bulb replacement. Found low voltage wire insulation at condenser cracking. There is no bare wire showing. On the next maintenance this should be checked for any further deterioration. System is clean, sanitized, and operating properly at this time.
No heat Low voltage control signal not leaving the control board to energize the heat kit. Low voltage is ok from thermostat to the board. The board needs to be replaced. Unit is under warranty.
install tear out old air handler replace with new Ruud air handler tie an old copper low voltage high voltage dying plenum new thermostat tear out older condenser replace with new condenser on new pad thai down four corners Thai and high voltage low voltage and copper startup everything work in perfect condition test in heat and cool modes customer happy and paid
Tara all ductwork replaced with new plenum in return plenum new oxidizer on return plenum tie into the ballast for UV light in the plenum reroute copper and drain line for installation of new electronic filter
Upon arrival customer showed me an ac system in the garage that needed to be tuned up. The evap coil is dirty and will need a pull and clean. Cleared the condensate line with nitrogen, shop vac and solvent. Checked the system for proper amp and voltage. Went to the condenser and checked for proper amp and volts. The capacitor is in factory specs. Add a surge protector.
Performed maintenance on split system. Cleaned vacuumed drain pan and drain line. Adjust safety float switch and check operation. Check thermostat calibration and filter location. Inspected evaporator coil and blower motor operation. Cycled system in heat strip and inspected condenser coil. Check refrigerant levels and check test start up components. Unit is cooling well and drains at this time. Customer has 59.95 coupon. Customer is satisfied.
Completed maintenance on 3 split systems in the home. 2 newer systems are inverter / communicating, system 3 is traditional. Issues found: Drain pan on a/h 3 not installed correctly. No float switch on a/h Found capacitor on cond unit 3 weak 30 of 45 mfd Found growth in all 3 units airhandler. Homeowner purchased a 3 system maintenance program today. She has agreed to repairs and would like me to return 8am Wednesday morning ( 11/17/21 ). She will leave a check for balance that morning. Her handyman Howard will be at the home to let us in. We will need to build a quote for drain pan repair.
Trane unit #1 Upon arrival customer showed me and air handler in the garage that needed tuned up. Checked for proper amp and voltage. Cleared condensate line with nitrogen, vac and water. The evap coil is clean. The evap coil pan is rusted and falling apart. Went to the condenser and checked for proper amp and voltage. The contactor had some pitting to it and the capacitor was reading low. We also have a 14 degree split. Customer does donâ€™t want to throw money into a 25 year old system. Mention to customer we can come out tomorrow to give and estimate. She said she will call in the morning to schedule a time after she talks to her husband. Bryant unit #2 Upon arrival customer showed me a unit in the garage that needed to be tun d up. Checked for proper amp and voltage. The evap coil is clean. Cleared the drain with shop vac, nitrogen and water. Went to the outdoor condenser and checked for proper amp and voltage. The contactor is good. The 70/7.5 capacitor was reading low. Replaced
Upon arrival technician found capacitor had failed on compressor side, recommended replacement of capacitor client agreed. Technician measured refrigeration and sub cooling unit operating Within design parameters at this time.
Unit running upon arrival customer vaccumed out drain line. Owner said that itâ€™s an HOA issue so I did not perform any further drain clear out. If we get a call out again for drain issues we will have to clear it out and charge for it.