Palm Harbor, FL HVAC Experts
for Palm Harbor, FL
Very polite and professional, good service
Baker - Palm Harbor, FL
Very professional and polite
Install 3.5 ton duct system. All new flex. All new mixing boxes. 3 returns cut in and add. 2 new supply grilles. 1 new return grille 24x24.New plenum in attic. Hang and mastic everything.
Uppon my arrival found the evaporator coil completely frozen. I started the defrost process and changed all filters. I added 8.2 pounds of r410a refrigerant out of jug #179. I also used leak stop to try and seal up the leak. Customer said that she has someone come out one a year and add refrigerant to the system but hasn't got it done in a few years. I got my delta T to 21.1Â°. I found a weak capacitor on the od fan motor ( it's a 7.5 mfd reading 5.78). I recommend we keep monitoring the refrigerant levels and replace the run capacitor for OD fan motor. I put together an estimate and loaded my pictures to service titan and cleared the drain line. I left the unit in good working condition. The customer use the 25$ off coupon.
Found supply plenum came off air handler in tight attic. There were no support straps on plenum box. I supported and seal supply box. I checked pressures and electrical components, good. Let System in good working order..
Performed pull and clean. Coil was extremely impacted. System passes pressure test and achieved proper vacuum. Released and performed start up procedure. System is working properly. Cleared the drain.
I rewired the germicidal UV light. The copper and drain is in front of the unit but you can take the pannel door off. It's not easy but doable and the service pannel is easily accessible. The coil is impacted with construction dust and needs to be pulled and cleaned. The unit was installed in March and they have been doing some remodeling inside. The customer said they have been changing the filter and shutting unit off while working. The evidence points in the other direction. I recommend we pull and clean the coil and order more replacement filters for the electronic air filter. Cycled and inspected equipment. Found all previous notes accurate. Need to schedule coil cleaning.
I found the start capacitor was weak, replaced. The system was 1lb low on R22, added. I hosed down condenser coil of pollen. They purchased a senior care . The system has wear and tear. The system doesnâ€™t have much life left.
I found the drain line was restricted. I vacuumed out with cleaner. I vacuumed the water out of the secondary pan (10 gallons). I checked pressures, good.
Performed system tune up. Inspected all electrical components and found no issues except that the core for the Reme halo had failed. Cleaned the blower wheel by customer request. Contact customer with pricing on a Reme halo core replacement. Cleared the drain line, left system running
1 year supply 20x20 EAC filters. I showed the owners how to replace the filter and clean the EAC.
9000 btu mini-spli installed with new concrete pad 17" from the wall Couldn't start the unit do to no power coming in to the disconnect Customer will pay after the job gets completed. We performed start up procedures and tested the drain line. I collected a payment from the customer. Everything is in proper working condition. I emailed the invoice to the customer and she want the office to email her the invoice from the split system install.
Installed vertical 3 1/2 ton 16 seer Amana four piece Plenum new word for Stan top relocated filter back supply Grill installed UV light and electronica air cleaner system started up and charge to factory spec air handler unit has number 10 wire on an 8KW heater which requires a 50 amp breaker customer and Bill will need to speak about possibly getting Don out for circuit or a smaller heater to pass inspection