Palm Harbor, FL HVAC Experts
for Palm Harbor, FL
I found the start capacitor was weak, replaced. The system was 1lb low on R22, added. I hosed down condenser coil of pollen. They purchased a senior care . The system has wear and tear. The system doesnâ€™t have much life left.
I found the drain line was restricted. I vacuumed out with cleaner. I vacuumed the water out of the secondary pan (10 gallons). I checked pressures, good.
Performed system tune up. Inspected all electrical components and found no issues except that the core for the Reme halo had failed. Cleaned the blower wheel by customer request. Contact customer with pricing on a Reme halo core replacement. Cleared the drain line, left system running
1 year supply 20x20 EAC filters. I showed the owners how to replace the filter and clean the EAC.
9000 btu mini-spli installed with new concrete pad 17" from the wall Couldn't start the unit do to no power coming in to the disconnect Customer will pay after the job gets completed. We performed start up procedures and tested the drain line. I collected a payment from the customer. Everything is in proper working condition. I emailed the invoice to the customer and she want the office to email her the invoice from the split system install.
Installed vertical 3 1/2 ton 16 seer Amana four piece Plenum new word for Stan top relocated filter back supply Grill installed UV light and electronica air cleaner system started up and charge to factory spec air handler unit has number 10 wire on an 8KW heater which requires a 50 amp breaker customer and Bill will need to speak about possibly getting Don out for circuit or a smaller heater to pass inspection