Madeira Beach, FL HVAC Experts
for Madeira Beach, FL
Gomes - Madeira Beach, FL
Upon arrival found two weak capacitors and a failed fan motor. Motor and capacitors need to be replaced. Customer is aware that when this parts are installed more testing has to get done to insure system is working properly. Installed a new OEM condenser fan motor and replaced the two weak capacitors, I recommended a surge protector to better protect the unit. Customer moved forward. Performed start up procedure, left system in good working order.
The drain line outside was in a bad spot and would get knocked out of place by her gate and cause it not to drain properly. We repaired and rerouted the drain and checked for proper drainage. No service charge (Per Jason) only charged for minor drain line repair.
I performed a maintenance. I checked pressures, electrical components and flushed drain line.. The contractor is pitted/ burnt, replaced before it fails.
Completed member tune up #1. The airhandler uv bulb is blown. The condenser dual capacitor is good but the terminals are rusted, the disconnect is old and rusty and the suction line armorflex is old and falling apart. The location is on the beach and the salty air has caused a lot. The customer is from up north and come back and forth every once in a while. Customer approved the work. We replaced the uv bulb, dual capacitor (warranty), condenser disconnect and reinsulated the suction line. We left the system in good running order. *Customer used a $50 coupon*