Check Out Our Work in Kenneth City, FL
Total Air provides air conditioning, heating, water heater and plumbing services to the residents of Kenneth City, FL and the surrounding areas. Read our reviews and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Kenneth City, FL.
for Kenneth City, FL
Customer complaint alert on thermostat out door sensor not working Upon arrival located thermostat error was not present, gained access to tech option in thermostat found that error has been repeatedly going on and off. Located condenser on side of house found the led on the condenser (outdoor) control board has failed LED does not work, continued inspection found burn marks on the back of the board, the transformer has also melted partly and is intermittently working. System is running at this time. Will need to replace the condenser (outdoor) transformer and the condenser (outdoor) control board. Customer would also like a surge protector put on the condenser when board and transformer is installed. Will have to return to install condenser control board and transformer. Follow up 2/24/23 Replaced inverter board and power conditioner/transformer. Ran system test successfully. Home owner approved surge protector installation. System operating normally at this time.
No cool. Drain line backed up and float switch is bad. Cleared drain line and replaced float switch. Tested drain and float switch successfully. Homeowner signed up for maintenance program today. Office to reach out to schedule first maintenance visit. System cooling and draining normally again.
Customer concerned about unit not cooling properly. Located the condenser fan motor is not running properly/ reverse spinning. Checked capacitor and capacitor has tested weak. Recommend new capacitor replacement in condenser unit. Changed thermostat batteries. Unit is running at this time. Customer has declined capacitor at this time.
Called out today due to no heat. Upon arrival fan would run but the heat strips would not. Found that the thermostat has failed. Gave options for programmable vs client supplied. She ran across the street and grabbed a non programmable stat and had me install it for her. She’s lived in the home for a year and has yet to have preventative maintenance performed. Educated her on the importance of annual maintenance. Enrolled in maintenance agreement and applied member discount to todays repair. Installed thermostat and cycled system on heat and cooling. Went through the system and found that the capacitor in the condenser is below manufacture specifications. Gave options for preventative repairs but she is going to wait until maintenance. Equipment is operating at this time. Jeff is coming out to give options for replacing the 24 year old machine. Thank you for always choosing Total Air!
Miscellaneous - house is up for sale, rodents have eaten some of the duck work want a quote to fix. Aware of the 79.95 service call Checked ductwork connections and inspected equipment cabinet. The attic has flexable ductwork that has been damaged and broken. All flexable ductwork needs to be replaced. I have found the flexable duct old and smashed, air blowing in the attic. 6 flexable runs will need to be replaced. Needs the 3bags of 7” flexable ductwork replaced and 1 bag 5” flexable ductwork to the bathroom. Have mentioned the attic insulation is very poor and needs to be insulated. Customer is interested to have quotes for attic insulation after the flexable duct replacement. (No collars needed) 3 bags 7” flexable duct 1 bag 5” flexable duct Mastic and brush Hanging cloth strap 3 hrs Customer is interested of quote for blown in attic insulation.
Upon arrival to Mini split head cleaning I was shown to mini split head in upstairs bedroom. Took apart mini split head and pulled out the fan and drain pan. Took fan wheel outside and cleaned with cleaner and a hose. Cleaned coil with solution and foaming cleaner and wiped down entirety of the unit. Reinstalled fan wheel and put unit back together and ran unit in cooling modes. This unit is running much more efficiently and pushing way more air throughout living space than it was before. Spoke with homeowner and is happy with work performed. Collected payment/signatures and left. Job complete.
Arrived at customer's house for condenser nonstop running. On arrival customer showed me to condenser. Thermostat inside was off customer turned breaker on and condenser turned on. Tested and confirmed there was no 24 V call from the thermostat. Moved the column that controlled the individual contacts and they released. The plastic side in the middle is getting stuck. The beads are not welded closed. No pitting is seen. Explained this to customer and told her she needed a new contact her. Customer agreed. Installed new contact or. Started off unit about 5 Times. Unit shut down when it was supposed to with new contactor. Confirmed with customer and Customer is pleased with work performed. Pointed out to customer that they did not have A surge protector on the system. Explained the benefits of our surge protector. Collected payment and signatures and left. Customer happy.
Performed preventative maintenance. Took amperage of indoor blower motor and electric heat strip. Calibrated and tested thermostat. Inspected and tightened electrical. Replaced filter customer provided. Cycled heating and cooling. Took temperature difference. Cleared drain pan and drain line. Located condenser on side of house. Inspected and tightened all electrical. Checked capacitor. Checked refrigerant levels. Took amperage of compressor and outdoor motor. Cleared debris from condenser housing. Rinsed condenser coil. System operating to factory standard. Recommend blower wheel cleaning. Spoke to customer and showed the biological growth, customer opted with blower wheel cleaning.
Upon arrival to scheduled maintenance I was shown to an A/H unit in a closet. Took off panel door to inspect all electrical components amp draw/voltage readings as well as check the evap coil. Evaporator coil was clean and readings of electrical equipment were within range of factory specs, except for the run capacitor that powers the fan motor. Capacitor was running low and below rating, I suggested to homeowner that we go ahead with replacing to ensure she wouldn’t be without cool air down the road. Installed new turbo 200 mini. Went to outdoor C/U to check Freon levels as well as inspect and collect readings of all electrical components connections. This unit is equipped with a new turbo 200 capacitor and contactor that are fully operational at this time. Freon levels were on point. Cleared drain with vacuum and followed with solution to ensure drainline was clear and properly draining with unit in operation. Overall this unit is operating very well, spoke with homeowner
Arrived at customer's house for system inspection. On arrival customer showed me to airhandler system. Under evaporator coil was clean. Inside air handler cabinet was infected with bio growth. Pointed out to customer and suggested and IAQ.Turned on unit and unit was producing proper Delta T. Went outside to condenser and open electric cabinet. Found capacitor below acceptable range. Pointed it out to customer and suggested we change. Customer agreed. Changed out capacitor and unit now runs fine. Vacuumed out drain line. Unit is currently not equipped with a surge protector. Pointed it out to customer and explain benefits of surge protector. Created estimate. Collected payment and signatures from customer and left. Customer happy.
Arrived at customer's house for system inspection. On arrival home owner showed me to air handler unit. Opened up cabinet and saw bio growth. Unit is equipped with a surface UV light. Bulb is past change date though. Pointed out to customer and suggested they get bulb changed. Customer is waiting for a loan to come within the next few weeks. Will call us to get bulb. Also informed customer of upgraded UV light. Left literature with customer and customer will consider upgrading with loan money. Also informed customer of our financing options. Unit was producing proper Delta T. Next went out to condenser unit and opened electric cabinet. Tested all components. Contactor sending proper voltage. Capacitor within acceptable range. Vacuumed out drain line. Unit is currently not equipped with a surge protector. Informed customer of this and suggested he get 1. Created estimate. informed customers that their plan was running out by the end of this month. Suggested they signed up with plan. Cu
Upon arrival customer showed me an ac unit in the laundry room that needed tuned up. The evap coil is clean. Cleared condensate with shop vac and water. The Uv Light is working good. The thermostat was programmed to replace the bulb every 6 months. I reprogrammed to be replaced every 24 month. Checked all amps and volts. Went to the condenser checked all amps and volts.
Performed preventative maintenance tune up. Checked blower motor operation and inspected evaporator coil condition. Checked safety float switch and inspected drain line. Cleaned vacuumed drain pan and drain line. Checked thermostat calibration and inspected filter location. Checked refrigerant levels and check test start up components. Cleaned debris from condenser and rinse compressor deck. Unit is cooling well and drains at this time. Customer declined membership at this time. Customer has coupon for maintenance tune up.
EAC Media pad replacement.
Tear out existing air handler replace air handler on new stand hook up existing plenum high voltage low voltage drain line new thermostat new heat shield and mechanical fasteners tear out condenser replace padlock pad new condenser tired existing copper high voltage low voltage drain line nitrogen test 400 PSI vacuum down to 500 microns start up everything's working in perfect condition added 3 lb of 410A freon
Upon arrival customer told me the ac was not working. The indoor fan was on and also the condenser was running. Put my gauges on and it was almost empty of all freon. Customer had another company add freon on 7/25/22 and another company add freon on 8/23/22. We can not add any more freon. Comfort advisor Coming out to give quote.
Customer had a plastic bag sucked into the opening on his return. Bag was stuck on stuck on evaporator coil. Remove bag and start it up unit. Unit started fine. Check in with customer and customer was happy. Unit now cooling properly. Collected payment and signature and left.
Upon arrival customer told me the ac was not running outside. Found a bad 35/5 capacitor which made the unit go in lock out mode replace with a turbo 200. Restored ac to home
Customer concerned about unit leaking water from unit plenum. Check blower motor operation and inspected evaporator coil condition. Checked drain pan and drain line, located clogged drain line. Cleaned vacuumed drain pan and drain line. Treat with solvent and prime drain line. Suggest new drain line in garage under cabinets to and thru front exterior wall to front planter. Pvc Drain pipe and hole thru concrete.
No cool System tripped hard lock out due to low refrigerant pressure. Refilled system and leak checked condenser. Found leak at low pressure sensor head. Office will call with repair quote and to set appointment for repair. Homeowner signed up for TAPS maintenance program. After repair is completed, we will complete the first maintenance for the year. System is cooling for now.
Upon arrival customer showed me an air handler in the closet that needed turned up. The evap coil is dirty and needs to be pulled and cleaned. Customer Denied work. Cleared the condensate with nitrogen and solvent. Checked the system for proper amps and voltage. Went to the condenser the check proper amps and voltage.
Attic Upon arrival customer showed me an ac unit in the attic that needed to be tuned. The evap coil is clean. Cleared condensate with nitrogen and solvent. Checked the system for proper amp and voltage. Went tot the condenser checked the system for proper amp and voltage. Found the 45/5 capacitor week. Replaced it with a Turbo 200. The contactor had a little burn marks and customer Denied. Also the compressor is over amping. I recommend a hard start and customer Denied. 19 degree delta T Mini split The evap coil is clean. Used shop vac to clear condensate drain. Checked the system for proper amp and volt. System is running at a 18 degree delta T.
Amana ASZ14 Pump 3 Ton. Install new air handler on new stand. New disconnect installed at air handler. New flex supply in closet. Install t6 pro thermostat. Breakers changed according to size. Condensor installed on pad block pad. Customer would like Bailey to email her a letter for her insurance company regarding the lightning damage that led to the unit needing to be replaced. Customer satisfied!
Upon arrival customer showed me the ac unit that need to be tuned up. The evap coil is clean. Clear the drain line with nitrogen and water. Checked all components for proper amp and voltage. Went to the condenser and checked for proper amp and voltage. Found a contactor with Pitt marks and a capacitor bad. Replaced the contactor and 35/5 capacitor with a turbo 200. We have a delta t of 18