Kenneth City, FL HVAC Experts
for Kenneth City, FL
Upon arrival found drain line clogged. Cleared drain line and pan. Ran a cleaner through the drain line and then water after to try and loosen up some of the buildup in the line. Offered membership and we did not move forward at this time. Inspected the rest of the system after. Left system in good working order.
The condenser dual capacitor has failed. I replaced the capacitor (warranty), cycled and monitored the system for proper voltage, amps, pressures and temperatures. I left the system in good running order. Customer declined renewing her TAP membership at this time.
The condenser dual capacitor has failed. I replaced it, cycled and monitored the system for proper, voltage, amps, pressures and temperatures. The airhandler canâ€™t be accessed right now because itâ€™s blocked by a wall. I informed her there needs to be access for the airhandler and she will have her husband make an an access panel for it. Customer purchased a TAP senior membership. She has a lot of landscaping construction work going on and will contact us when itâ€™s finished and schedule her first tune up. I left the system in good running order.
Performed complete tune up on AC system. Checked all electrical components, system pressures, temperature differentials, coils and cleared drain line. Upon inspection of air handler, we found the UV bulb to be out but the customer politely declined a replacement bulb We also found the delta t to be 16 degrees and system pressures were low so we determined the system to be about 2-3 lbs low on refrigerant. The air filter was also impacted so we recommended the customer replace it. Upon inspection of condenser, we found the capacitor to be weak so we recommended a turbo warranty capacitor. Customer agreed to the repairs so we installed the Turbo 200 5 year warranty capacitor as well as charged the system with 1.3 lbs of 410A from jug #145. System was left with a 21 degree split but we will continue to monitor refrigerant levels in the future. Customer also signed up for Prime Senior membership so we will be counting this towards the first tune UP so please make
I installed the air cleaner and wired up the fan 24v. I showed Dawn how to replace filter.. customer already payed..
I performed a complete tune up on the ac system and cleaned out the drain line. I checked all electrical components and motors. Found evaporator coil is dirty and can be cleaned in place. Run cap is weak and should be replaced, also dual capacitor is weak and should be replaced. The contactor is pitted. My delta-T was at 16Â° due to dirty coil. The customer is complaining of smoke smell when the unit comes on. I recommend we clean the coil the ductwork and add a UV light. I built an estimate for required repairs and enhancements. The unit is 25 years old. I spoke to the customer and they want an estimate to replace the unit. We set up an appointment for Bill to come out tomorrow between 1-3. Left the system in working condition.
I found the condenser fan motor was over amping, the contactor was pitted/ burnt, the dual run capacitor was weak on MFDâ€™s, replaced parts. I sanitized the air handler of growth and installed a pure airX uv light. Dawn will like to have a electronic air cleaner which I measured and add an extra pure airX uv light in return. I will wire into the ballast. The ballast has a life time warranty, bulbs have a 2 year warranty.