Kenneth City, FL HVAC Experts
for Kenneth City, FL
Upon arrival found thermostat batteries in backwards. Switched batteries and tested operations. Left system in good working order.
Amana ASX16 AC 3 Ton. Install 3 ton air handler on new stand. Install uv light. New nest thermostat. Breakers changed to 35 amp. New condensor on new pad. Unit charged to subcool. Customer satisfied!
Technician went over system operations along with checking on electronics and refrigeration no faults found. When discussing issues found unit would turn itself off for no reason. Technician suspects infrared signal from other devices affecting this head unit. Two systems signed up for maintenance agreement.
Upon arrival checked motors, electrical components, and pressures. Cleared drain line and added Nubrite. Recommended UV bulb replacement and customer declined. Created estimate and emailed UV BULB REPLACEMENT TO CUSTOMER. DeltaT at. 21 degree split. Newer Turbo 200 recently installed. Renewed TAPS senior for customer. Left system in good operating condition.
Upon arrival system was not cooling, hot air was blowing from vents, checked refrigerant charge and found R22 system low on charge. Charged system to get them up and running, recommended a leak search, customer said they have already been quoted for a system we recommended being quoted for a new unit once again. Cleared drain lines. Left system in good working order.
Upon arrival system not operational technician found capacitor dead replace capacitor under warranty system is operational at this time. Recommend search protection at this home client to confirm with Office if she wants this.
15 Drop Duct System Tore out or duck system Moved supply grill in kitchen to be even with dining room living room area started to re-run ductwork will return Friday to continue on working Installed for Dr. system in the house cutting two brand new returns in both bedrooms and move supply Grill in kitchen started up system system running to factory spec customer satisfied paid in full
Uppon my arrival I found water inside the float switch. I cleared therein line and started the unit. I changed the filter and checked the coil. Coil is clean. Uppon further investigation found the dual capacitor extremely low. I got permission to replace with a turbo 200 5 year warranty capacitor. The air handler has a burnt out UV light ( it's the economy UV light). I asked if he wanted to replace but the customer politely declined at this time. I performed start up procedures and left the unit in good working condition. The customer signed up to our maintenance program so he could get the discounts. We need to schedule a tune up soon. I loaded my pictures and equipment information to service titan.
Install 1200 BTU air handler fan coil in master bedroom in new location per customers recommendation rand line height to existing stand for condenser on roof mounted new condenser Two existing stand modified existing stand to hold new mini split condenser perform pressure test in microns below 500 started up unit and performed all started procedures system running to factory spec instructed customer on usage of their new air-conditioning system collected payment change breaker customer satisfied also repaired drywall wall inside and repaired concrete wall outside
Install 3 ton 16 seer Bryant relocation brand new coffin box brand new supply and return plenums offset brand new 16 inch metal pipe for supply and return insulated and hung in garage ran a brand new three-quarter inch drain line installed brand new pad for condenser attached onto Copper attached on to terms that wire for relocation of air handler perform all started procedures including pressure test above 400 psi G vacuum below500 Âµm started up system and charge system to factory spec customer paid in full we will need to come out Monday to re-install a Wi-Fi Honeywell thermostat the thermostat we received out here is defective I temporarily installed a Honeywell T6 extra thermostat to get customer cooling customer satisfied with their new installation
Completed system tune up. Checked volts, amps, pressures and all electrical components. Checked thermostat operation. Checked air filter and evaporator coil. Cleared drain with cleaner. Found microbial growth in air handler and on bottom of coil. Recommended installing Remy halo to prevent growth and kill existing growth. We will sanitize when installed. Customer will call to schedule. Renewed membership. Left system in good working order.
Cycled and inspected equipment. Found compressor over amping and tripping breaker. Left system off. Customer requested quote to replace. Corey is scheduled today 9-11. Informed customer we would refund $79.95 service call fee. Customer wanted to know if we could refund some of the motor cost since she just recently purchased the motor. I informed customer that would be a question for Corey.
Cycled and inspected equipment. Found condenser missing parts ( capacitors ), no access to air handler due to boxes in front of air handler closet, and system is 31 years old. Advised customer we could replace parts but we would not know for sure if other problems could arise due to age and condition of equipment. Left system off for now. *note* advised customer if they move forward with the system replacement we will credit the $79.95 service call fee for today. Scheduled Corey from 5-7 p.m. today to give customer quote to replace. Customer is not cooling. Recommend: new equipment due to cost of repair, age, and overall condition of equipment.
Upon arrival found drain line clogged. Cleared drain line and pan. Ran a cleaner through the drain line and then water after to try and loosen up some of the buildup in the line. Offered membership and we did not move forward at this time. Inspected the rest of the system after. Left system in good working order.
The condenser dual capacitor has failed. I replaced the capacitor (warranty), cycled and monitored the system for proper voltage, amps, pressures and temperatures. I left the system in good running order. Customer declined renewing her TAP membership at this time.
The condenser dual capacitor has failed. I replaced it, cycled and monitored the system for proper, voltage, amps, pressures and temperatures. The airhandler canâ€™t be accessed right now because itâ€™s blocked by a wall. I informed her there needs to be access for the airhandler and she will have her husband make an an access panel for it. Customer purchased a TAP senior membership. She has a lot of landscaping construction work going on and will contact us when itâ€™s finished and schedule her first tune up. I left the system in good running order.
Performed complete tune up on AC system. Checked all electrical components, system pressures, temperature differentials, coils and cleared drain line. Upon inspection of air handler, we found the UV bulb to be out but the customer politely declined a replacement bulb We also found the delta t to be 16 degrees and system pressures were low so we determined the system to be about 2-3 lbs low on refrigerant. The air filter was also impacted so we recommended the customer replace it. Upon inspection of condenser, we found the capacitor to be weak so we recommended a turbo warranty capacitor. Customer agreed to the repairs so we installed the Turbo 200 5 year warranty capacitor as well as charged the system with 1.3 lbs of 410A from jug #145. System was left with a 21 degree split but we will continue to monitor refrigerant levels in the future. Customer also signed up for Prime Senior membership so we will be counting this towards the first tune UP so please make
I installed the air cleaner and wired up the fan 24v. I showed Dawn how to replace filter.. customer already payed..
I performed a complete tune up on the ac system and cleaned out the drain line. I checked all electrical components and motors. Found evaporator coil is dirty and can be cleaned in place. Run cap is weak and should be replaced, also dual capacitor is weak and should be replaced. The contactor is pitted. My delta-T was at 16Â° due to dirty coil. The customer is complaining of smoke smell when the unit comes on. I recommend we clean the coil the ductwork and add a UV light. I built an estimate for required repairs and enhancements. The unit is 25 years old. I spoke to the customer and they want an estimate to replace the unit. We set up an appointment for Bill to come out tomorrow between 1-3. Left the system in working condition.
I found the condenser fan motor was over amping, the contactor was pitted/ burnt, the dual run capacitor was weak on MFDâ€™s, replaced parts. I sanitized the air handler of growth and installed a pure airX uv light. Dawn will like to have a electronic air cleaner which I measured and add an extra pure airX uv light in return. I will wire into the ballast. The ballast has a life time warranty, bulbs have a 2 year warranty.