Dunedin, FL HVAC Experts
for Dunedin, FL
Amana ASZ14 Heat Pump 3 Ton. Install air handler on new hanging kit. Install uv light. Change breakers according to size. Install t6 thermostat. New condensor on new pad. Customer satisfied!
Performed routine maintenance on older split system checked amps volts drain lines capacitors refrigerant pressure etc. system is starting to show its age would recommend system replacement in the near future. For now system is in good working order
Required Repairs: These are the minimum services required to get your system running today and does not include any recommended actions that I noticed. Recommended Service +: This includes the required repair to get your system running today and recommended service to items that I noticed also need some attention. I have also included solutions to extend the life of your system and protect it from future breakdowns. I am able to complete these tasks today at a discounted rate, shown below. Air handler inspection complete volts amps are within range ECM Tate motor. Coil bright and clear. Economy UV bulb has burnt out recommend replacement client has agreed. Technician does not have bulbs in stock on truck must return to install. Condenser inspection complete volts amps and microfarads within range contactor bright new capacitor recently installed. This unit is operating at this time no faults found. Must return with economy UV bulb to install. Tuneup complete.
Tear out old unit install new 3 ton 15 Seer heat pump on new hurricane pad new disconnect 4 condenser install new air handler on new hanging kit hookup plenums with new heat shield on Supply and return mechanical fasteners splice onto low voltage wire up wiring two flow switches one in line one pan tape and Mastic plenums secure drain lines and drain pan put P-trap outside start up everything running in perfect condition collect and got signatures finished job
Found not heating due to bad 10mfd blower motor run capacitor. Replaced with turbo mini. Checked operation. Left system operating. System in poor condition. Lots of microbial growth and lots of rust and corrosion.
Cleaned upstairs and downstairs evaporator coilâ€™s downstairs removed wet section bottom of return replaced and sealed cleaned and sealed upstairs air handler as well as downstairs air handler installed UV 24 V system in each air handler collected payment customer satisfied
I performed a maintenance on both systems. I found some growth on evap coils. The coils/ primary pan pans need to be cleaned in place. I sprayed some cleaner/ sanitizer inside air handlers. I checked pressures, the 2nd fl system is 1lb low on 410a. My superheat is 33degs. I hosed down condenser coils of pollen. I vacuumed out drain line with cleaner. The 2nd fl drain line was very dirty. We discussed about uv lights. They will like to move forward on the economy uv light on each air handler. The 1st floor return plenum bottom base has some growth and at one time water was dripping and ruined the bottom base. Need to put in new bottom base with a new duct board, then sanitize the box.. The second floor system does have wear and tear due to age.. The office will reach out to set up appointment for work that needs to get done.. Doug will like the phone number to our duct cleaning guy we use. He is interested in having the ductwork cleaned.
Upon arrival performed maintenance. Inspected all electrical components, coils, pressures, and cleared drain line. Found both UV bulbs burnt out. Found the dual run capacitor reading weak MFD and the contactor pitted and burnt. Recommended on replacing these parts. We moved forward with the contactor and capacitor. The UV light cannot be found so we didnâ€™t move forward on replacement of the bulb or a new UV system. Left system in good working order.
Upon arrival found system low on 410a refrigerant. The pressures were really low so I recommended a leak search. We moved forward on that. Found the leak in the copper line going to the compressor. The compressor has a hole in it as well. Gave quote for a compressor changeout and refrigerant but Corey will be out tomorrow 8/18/20 at 8am to give an estimate on a new system so they can way their options. System is not running.
Upon arrival found that the condenser fan motor had locked. Due to being after hours and supply houses closed offered a rescue rental but customer declined. I told her we will contact her on Monday for pricing approval and scheduling to replace the motor. Left system on the OFF position at the disconnect. Note: Contact customer with pricing and for scheduling Monday ASAP.
I wiped down and sanitize the inside of the air handlers. I installed the pure air X uv light on both systems and tested operation. I left the systems in good working order.
I replaced the 1st fl thermostat with the Ecobee. I tested cooling operation. I recommend on installing uv lights to kill growth and prevent growth inside the air handlers. It kills mold, bacteria and viruses.. i will give a follow up call.