South Pasadena, FL HVAC Experts
for South Pasadena, FL
Athena - South Pasadena, FL
Wonderful professional service
Lyninsouthpasadena - South Pasadena, FL
Jason and Andy were extremely courteous and knowledgeable! Very prompt and efficient. Thank you. Will highly recommend
Amana ASX14 AC 3 Ton + AMEC Furnace 60,000 BTU Installed 3 ton 14 seer Amana gas furnace furnace on existing stand modified stand to fit new furnace and modified supply Plenum to fit new furnace and added heat shield flush copper flush drain installed I wave in gas furnace sealed gas furnace condenser sat on existing roof stand system held pressure over 400 psi G in vacuum below 500 Âµm started up systemIn charge to factory spec instructed customer on usage of their brand new air-conditioning system and brand new Honeywell T6 thermostat customer paid in full via two credit cards totaling balance on account breakers are appropriate customer satisfied job complete
Completed system tune up. Checked pressures, volts, amps and all electrical components. Checked evaporator coil and drain line. Found dual run capacitor well below factory specs and also found 2 pole contactor very rusted and corroded. Replaced capacitor with turbo 200 which carries a 5 year warranty, replaced contactor and signed customer up for taps annual maintenance membership. Used todays tune up as 1 of 2. Left system in good working order.
Recommended Repairs: This includes the minimum required repair to get your system running today and recommended service items that I noticed also need attention. I am able to complete these tasks today at a discounted rate, shown below. Upon arrival found consensate pump and thermostat failed, so went ahaead and replaced both the thermostat and condensate up, went through start up procedure and both replaced items functioned properly, checked condenser pressures, amp draws, and electrical components, cleared drainline, took picture of evaporator coil and uploaded model and serial numbers for both units to ST, instructed owner how to use thermostat and what each light means for condensate pump. Left system in proper working order.
Cycled and inspected equipment. Found drain line restricted and system off on safety switch. Also found dual capacitor weak, hard start kit weak, contactor pitted, and supply plenum contaminated with bio growth. Cleared drain line, Installed a new dual capacitor, hard start kit, contactor, and pure air x whole house germicidal unit. Customer also approved maintenance agreement. Left system in good working order.
Drain line was restricted and tripped the float switch. We flushed and cleared the drain line, cycled and monitored the system for proper electrical, pressures and temperatures. We left the system in good running order.
The system is completely empty of refrigerant. The system is old (2003) and theyâ€™re selling the house. We talked about options of performing the leak check, if itâ€™s repairable and recharge with R427A. I gave them a quote. I highly recommend replacing the system due to age, cost of repair and a new system w/ warranties will up the value of the house. Estimate is scheduled for tomorrow 11 - 1 time frame. They informed me they want the cheapest system possible.
New 1.5 ton installed front draw with 5kw heater , metal 90 at the condenser , job went great , customer satisfied, left the system running in perfect condition.
Upon arrival found float switch tripped. Cleared drain line and ran a cleaner through the pvc with the vacuum on the other end to create a vortex. Had a temperature differential of 19. Left system in good working order.
Upon arrival found dual run capacitor failed. Condenser fan motor had oil on it from the bearings being failed. Also the condenser coil is falling apart. Need to schedule Bill our supervisor to come out and give an estimate to replace the system. Bill will be coming out today with a 30 minute prior call. This being a bard condenser the parts will be hard to get on it and expensive because it is an r22 system. They system is 24 years old.