South Pasadena, FL HVAC Experts
for South Pasadena, FL
Cycled and inspected equipment. Found drain line restricted and system off on safety switch. Also found dual capacitor weak, hard start kit weak, contactor pitted, and supply plenum contaminated with bio growth. Cleared drain line, Installed a new dual capacitor, hard start kit, contactor, and pure air x whole house germicidal unit. Customer also approved maintenance agreement. Left system in good working order.
Drain line was restricted and tripped the float switch. We flushed and cleared the drain line, cycled and monitored the system for proper electrical, pressures and temperatures. We left the system in good running order.
The system is completely empty of refrigerant. The system is old (2003) and theyâ€™re selling the house. We talked about options of performing the leak check, if itâ€™s repairable and recharge with R427A. I gave them a quote. I highly recommend replacing the system due to age, cost of repair and a new system w/ warranties will up the value of the house. Estimate is scheduled for tomorrow 11 - 1 time frame. They informed me they want the cheapest system possible.
New 1.5 ton installed front draw with 5kw heater , metal 90 at the condenser , job went great , customer satisfied, left the system running in perfect condition.
Upon arrival found float switch tripped. Cleared drain line and ran a cleaner through the pvc with the vacuum on the other end to create a vortex. Had a temperature differential of 19. Left system in good working order.
Upon arrival found dual run capacitor failed. Condenser fan motor had oil on it from the bearings being failed. Also the condenser coil is falling apart. Need to schedule Bill our supervisor to come out and give an estimate to replace the system. Bill will be coming out today with a 30 minute prior call. This being a bard condenser the parts will be hard to get on it and expensive because it is an r22 system. They system is 24 years old.