Air Conditioning Service In Clearwater
When you need air conditioning service in Clearwater, the first thing you should do is call us at Total Air. Founded in 2003, we have quickly become the trusted AC repair company for St. Joseph’s Hospital and Autoway Dealerships, as well as many other residential customers. No matter if you need maintenance, repairs, or installations, we’ve got you covered! We sell and service all makes and models of HVAC units for both commercial and residential buildings. Our fast and reliable technicians will show up to your home or business on time, and will get you back to enjoying cool air in no-time.
One of the most important, yet most often forgotten air conditioning services we offer in Clearwater is preventative maintenance. Not only does this allow you the peace of mind that your AC will always be working efficiently, but you will be able to save money by fixing smaller parts as they wear down instead of dealing with giant repairs. Keeping your home cool during our hot summers can take up almost half of your monthly energy bills, so it only makes sense to have that machine running as efficiently as possible.
A typical Total Air maintenance check includes:
- Inspect thermostat. We will ensure the set temperature matches the room’s actual temperature.
- Check electrical components. Issues with the electrical connections can cause the unit to be unsafe and prone to needing more expensive air conditioning services.
- Clean coils. The condenser and evaporator coils can get dirty which will increase your energy usage while reducing the AC unit’s ability to cool your home.
- Check filter. This is what keeps the air in your home clean and healthy for your family to breathe. How often it needs to be changed depends on many factors including outdoor allergens and if you have pets that shed. Our trained air conditioning service technicians will know exactly when it needs to be replaced.
- Review system controls. This ensures the unit shuts on and off when it is supposed to, and that everything is working correctly while it is cooling your Clearwater home.
We can create a custom maintenance plan for you, and if you become a Preferred Customer you gain many benefits including semi-annual tune ups, priority services, and discounted parts.
AC Repairs And Installations
Even with maintenance, you will eventually need to have repairs or replace your Clearwater AC unit. Luckily, with our regular checks, our technicians will probably be able to warn you when you expect this to happen so you won’t suddenly be without a cold house on the hottest day of the year.
Often times it can be difficult to know whether you should pay for a repair, or if you should replace the entire unit. Some common signs that you should call for air conditioning services include:
- A steady increase in energy bills
- Your house is humid
- Not all rooms in your home are the same temperature
- The unit is leaking
While some of these may not seem serious at first, if left alone, they can cause you to experience unexpected break downs. If you are facing any of these issues and your AC unit is more than 10 years old, it may be more cost effective to replace it with a new one. One of our Clearwater air conditioning service technicians would be happy to discuss the age old question of “repair or replace?” with you to decide which is best for your needs.
Total Air, Inc: Your Trusted AC Services Company
Here at Total Air in Clearwater, we want you to feel confident in the companies you hire, which is why we offer a 100% customer satisfaction guarantee along with affordable pricing. Whether you need preventative maintenance air conditioning services or an installation, we can help you! Even if you are experiencing problems at 9 pm on a Sunday, feel free to call us. We offer 24/7 emergency services so you never have to wait long for AC help!
For more information, or a free second opinion, call us today at 727-822-7700!
for Clearwater, FL
Gabbard - Clearwater, FL
Was very informative
Mount - Clearwater, FL
As usual Jason displayed great customer service! Arrived on time and had a mask. No complaints here. I don't want to say too much as I know it will go to his head. Also, I didn't get his name but his assistant was exceptional as well.
Vinson - Clearwater, FL
Diruzza - Clearwater, FL
Amazing response. Great technician. And Tabitha who took the appointment was amazing! I watch 40 condos here on Sand Key. I run into these problems all the time. U will always be my first call from Now on. Thank you! Bernard DiRuzza
Lang - Clearwater, FL
Excellent service from Total Air once again! On time...honest ...knowledgable techs that are always polite and professional.
Uppon my arrival I found the drain line completely restricted. And float switch was elevated therefore didn't shut the unit down. The filter was dirty and was contributing to poor drainage. I cleared the drain line and cleaned out the primary drain pan. I leveled out the float switch and left the system in proper working condition. I changed the filter and soaked up most of the water from the unit.
Upon arrival performed maintenance. Inspected systems electrical components, coils, pressures, and filter. Cleared condensate pump and line. Offered maintenance membership but was not interested at this time. Left system in good working order.
They had two surges last night. The variable speed blower motor and air handler circuit board failed. I also noticed the thermostat clicks into delay every 5 minutes. This is another issue. I put a quote together on replacing parts. I highly recommend on replacing the system due to age and high cost. Corey is coming out today @2:30pm or so. Corey will go over options and when we can perform the work.
I found a lizard shorted the defrost board. I bypassed to get cooling. I checked pressures, let the system run for 20 minutes. The system is 2lbs low on 410a. This will make the system run a little longer than what it should.I marked this up on 1st visit. Her concern is the the last person didnâ€™t mention about pressures and said everything is all set. I showed them and explained my pressures. I took pictures of my pressures. They said they want a second opinion!
Upon arrival found the condenser fan running and not the compressor. Further inspection revealed yhat one of the terminals had burnt out and the compressor had over heated. Cooled down the compressor and replaced yhe damaged wire. Performed start up procedures. System started right up. Note: Due to systems age, poor condition and recent history of issues I recommended a system replacement, Corey is going to provide a free quote next week.
Upon arrival found that the blower was constantly running and the nest was sat by someone for eco mode and fan on. Sat the thermostat to the proper settings and showed the realtor how to work the nest. Checked pressures and are in range. Left system running properly. (Roof hatch Lock box code 5936)
Installed brand new Lennix coil performed a pressure test and vacuum below 500 Âµm charge system to sub cool by factory spec system running properly collected payment customer satisfied
Cycled and inspected equipment. Found vertical air handler in closet doubled filtered. Also found drain line with very little pitch at air handler. Removed 2 dirty filters and installed a new customer provided 20x20x1 filter. Customer declined maintenance agreement and repairing drain line at this time. Customer did mention he would like to have the work completed during next scheduled maintenance. Left system in good working order for now. Recommend: repairing drain line to add more pitch for better drainage.
Completed precision tune up. Cycled and inspected equipment. Cleaned bio growth from air handler cabinet, cleared drain line, cleaned condenser coil, and installed a new pure air x whole house germicidal unit. Left system in good working order.
Upon arrival performed maintenance. Inspected systems electrical components, coils, pressures, and filter. Cleared drain line and condensate Pump. Found that the system was low on refrigerant. Gave different options moving forward. We are creating a history. Added 3 pounds of 410a refrigerant and tightened the service valves. We are going to monitor the pressures. We signed up for a membership and used today as visit number 1. Left system in good working order.
The 1st fl Lennox system is low on 410a. I performed a leak search. I found the leak at the evap coil , not repairable. The system is 8 years old. It should be under warranty if registered. I put a quote together on warranty and refrigerant. We need to call Lennox supply house .. I pulled the condenser disconnect until we replace coil. They donâ€™t really use the 1fl system that much. I renewed their membership..
Upon arrival performed maintenance. Inspected systems electrical components, coils, pressures, and changed filter pad. Cleared drain line and condensate Pump. We moved forward with membership renewal. She would like us to order. The media pads, the size is 22x20. Left system in good working order.
Upon arrival only issue with the thermostat was that it was constantly trying to connect to wifi. I disabled the pup up wifi connection screen and back to normal. If future buyer wants to connect to the wifi, it will still be possible at the settings. Went over the system and found that the coil was partially frozen. System was low on refrigerant. Added 2 lbs of r410a, if we ever return an is low again a full system leak search is recommended. System has no overflow safety and drain line is not serviceable. I highly recommend rearranging the drain line and installing a gloat switch to evade water damage due to sydtem overflow. Left system running properly.
Upon arrival cleared extremely clogged drain line. Used vacuum, nitrogen, and cleaner. Inspected operations after. Signed up for a membership on 2 systems. Left system in good working order.
Performed complete system tune up. Checked pressures, volts, amps, and all electrical components. Cleared drain line with nitrogen. Found blower run capacitor below factory specs. Recommended and replaced at this time. Also found liquid line dryer starting to rust. Found float with small amount of water, this is the second time we have cleared. Advised customer to contact building to have common drain line cleared. Left system in good working order.
Upon arrival performed maintenance. Inspected systems electrical components, coils, pressures, and filter, cleared drain line. The uv light bulb is burnt out. Offered our economy up light but didnâ€™t want to move forward. He would like to know when the distributor gets them in stock. (Itâ€™s a Fresh Aire Blue Tube Light). Recommended on a surge protector but was not interested. Offered membership but was not interested at this time. Left system in good working order.
I found the stat set to 78 degs and reading 78. The attic access was open. I vacuumed drain line with cleaner. I poured 2 gallons of hot water down drain line. We are coming out for a tune up soon.
Upon arrival found a failed dual capacitor at the condenser. Replaced the capacitor and performed start up. Fan motor did not kick on due to being I've heated. Culled down fan motors and it kicked on. Started storming out of no where, was not able to clear the drain line. Left system cooling.
Cycled and inspected equipment. Found system off on safety switch due to a restricted drain line. Also found dual capacitor weak, and contactor pitted. Cleared drain line, installed a new dual capacitor, and contactor. Was not able to gain access to air handler due to air handler in wall with plywood covering nailed. Left system in good working order for now. Customer approved 1 year 1 system maintenance. Recommend: access to air handler on next scheduled maintenance.
I found the thermostat is having some issues, it won't let me change the time and the unit doesn't shut of after it reaches 72Â°. The thermostat should be under warranty. It's a honeywell wifi pro 8000.i recommend we replace the thermostat with a new one. Office please call the customer to schedule an appointment and also let the customer know how much its gonna cost to replace. I left the unit in working condition. I didn't charge for service call fee due to the labor warranty. Installed a new pro-8000 thermostat. Found thermostat failed upon installation. Thermostat has a error code that stated internal sesor has failed and to replace thermostat. Installed pre existing pro-8000 thermostat. Upon start up found pre existing thermostat the reversing valve function is not operating and unit will run in heat only. Hot wired reversing valve at air handler. Left system in good working order for now. Recommend: new pro-8000 thermostat and disconnect reversing valve wiring 24v at air han
The system is from 1986. A surge tripped out system. I replaced weak dual run capacitor, start capacitor w/ relay, added 2lbs of 427a and installed a surge protector. I do recommend on replacing the system, but violet is very attached to the system.. she will wait till it dyes. I recommend on us performing a maintenance on system. I just got the system up and going. I couldnâ€™t do through the system thoroughly ( late at night)..
Cycled and inspected equipment. Found system operating upon arrival. Found drain line slightly restricted and condenser coil impacted. Customer has home under construction and has been trying to replace filter as often as needed. Cleared drain and cleaned condenser coil. Left system in good working order.
There are to air handlers side by side in closet. Below is water stain at return grill. The Lennox system was 4 lbs low on 410a, added. I tightened up service valves. We are creating a history. If the system leaks refrigerant again we need to perform a leak search.. I vacuumed out drain line, no growth came out. I also noticed the Trane unit beside the Lennox has air leakage at supply plenum and dripping water down the air handler.. I put quotes together..
Upon arrival found a clugged drain line. Cleared the restriction. Left system running.
I performed a complete tune up on the ac system and cleared the drain line with coil cleaner and water. I checked all electrical components and motors, refrigerant levels and temperature differentials. The condenser fan motor is overamping and the capacitor is starting to go weak. We will need to replace on our next visit ( it's a 45/5 reading 42.23/4.87). My refrigerant levels are good and I have a delta T of 21.5Â°. I loaded my pictures to service titan and left the system in proper working condition. I renewed the membership for the customer.