Air Conditioning Repair Pinellas Park FL
We understand how crucial it is to have your AC working at full capacity to give you the most comfortable environment. That’s why AC repair is a serious business and having a perfectly functioning Air Conditioner is so important. No matter how you may try to prevent any issues, it is bound to happen…There is no need to worry. Total Air Inc. provides expert Air Conditioner Tune-ups, AC preventative maintenance, and Air Conditioning Service and AC repair in Pinellas Park, FL and surrounding areas at an affordable rate.
Pinellas Park Air Conditioning Repair Experts
When the Florida heat pumps up, the last thing you need is for your air conditioning system to stop working. Sometimes your AC will act up and when it does, you can count on the quick and dependable AC Repair Service from Total Air Inc. We understand the importance of a fully functioning Air Conditioner and make your AC concerns a top priority.
At Total Air Inc. we are committed to keeping our customers in Pinellas Park and throughout the Pinellas Park area, cool and comfortable. Our experienced and highly trained HVAC technicians will provide the prompt, high quality air conditioning repair service needed to get your air conditioning systems up and running smoothly.
If your Air Conditioning unit is blowing hot air, making strange rattling sounds, or won’t turn on at all, give us a call here at Total Air Inc., (727) 822-7700. We will be there to solve any of your Air Conditioning problems. When it comes to Florida heat, AC Repair is crucial for any situation, large or small.
for Pinellas Park, FL
Raga - Pinellas Park, FL
The technicians were courteous and did the installation in a timely manner. I am happy you guys were able to accomodate me in such a short period of time. My only complain was when I checked behind the filter after they were gone where the leaking with my old AC happened, it was not cleaned up. I clearly remember when the guy who came and gave me an estimation of the price of the entire unit explained to me what they were supposed to do in the installation and that’s to include cleaning and putting something where the water was dripping with the old unit. When I took out the filter, the basin which was put there by the other technician who came to checked the leakage over a week ago was still in there. I don’t think the installer bother to even check below. It was still so dirty and still damp.
still no air
Briggs - Pinellas Park, FL
Good service, explained a lot. Unfortunately couldn’t help with air because of bad compressor. So it’s July, holiday, and weekend and we have no air, so it is hard to rate a great experience.
Merritt - Pinellas Park, FL
Very nice job and quick. Very satisfied
Great and efficient service.
Null - Pinellas Park, FL
I will recommend Total Air in a heartbeat 💓.
Professional service. Knowledgeable installation. Much helpful information.
Dolniak - Pinellas Park, FL
Cycled and inspected equipment. Found system off on safety switch due to a restricted drain line. Found air handler and immediate duct work with bio growth. Also found run capacitor weak, dual capacitor weak, and contactor pitted. Cleaned air handler cabinnet. Installed a new pure air x, run capacitor, dual capacitor, contactor, and cleared drain line. Left system in good working order.
Amana ASX14 AC 2 Ton tear out old condenser unit replace with new Amana asx14 AC 2-ton condenser on new hurricane pad strap down four corners pipe in splice onto electrical low voltage hookup hot voltage tear out old air handler on hanging kit put a new air handler on new hanging kit new Platinum new return plan on low voltage high voltage copper nitrogen test 250 psi vacuum pump Mike 500 micron start up everything working in perfect condition
Required Repairs: These are the minimum services required to get your system running today and does not include any recommended actions that I noticed. Required Repairs: These are the minimum services required to get your system running today and does not include any recommended actions that I noticed. Recommended Repairs: This includes the minimum required repair to get your system running today and recommended service items that I noticed also need attention. I am able to complete these tasks today at a discounted rate, shown below. Client already installed thermostat technician verified wires were correct, no faults found at unit in operation. Technician found main blower fan bearings have leaked oil within air handler recommended replacement of motor client has agreed. Technician noted micro biological growth within air handler client has declined at this time but high chance this will be done as client has seen the growth herself. Pricing for UV Included. This unit is operating
Cycled and inspected equipment. Found system almost empty on refrigerant indicating system has a refrigerant leak. Found contactor pitted, run capacitor weak, evaporator and condenser coils dirty, air handler and duct work contaminated with bio growth. Customer declined all repairs at this time and requested a quote to replace. Rich is scheduled tomorrow 12-2 for a free estimate. I also informed customer we would credit the 79.95 service call fee if customer decides to move forward itâ€™s be equipment installation. Customer is interested in financing. Left system off. Recommend: new equipment and duct work due to cost of repair, age, and overall condition of equipment.
Cycled and inspected equipment. Found drain line restricted, run capacitor weak, dual capacitor weak, contactor pitted, and immediate duct work contaminated with bio growth. Installed a new run capacitor, dual capacitor, and contactor. Customer declined maintenance agreement and pure air x. Left system in good working order for now. Recommend: maintenance agreement and pure air x whole house germicidal unit to eliminate and prevent bio growth.
Technician installed filter tested filter filter is filtering
Upon arrival checked motors, electrical components, and pressures. Cleared drain line and checked DeltaT at 21 split. Replaced failing run cap and hard start kit. Left system in good operating condition.
Found not cooling due to being off on float. Customer chose to clean drain line himself. Left system cooling at this time.
Cycled and inspected equipment. Found evaporator coil impacted, run capacitor weak, dual capacitor weak, contactor pitted, and system low on R410a. Customer declined repair and requested quote to replace. Left system as is for now. Scheduled Corey Friday 2-4 p.m. Recommend: new equipment due to cost of repair, age, and overall condition of equipment.
Upon arrival replaced condenser fan motor under warranty. Inspected operations after. Left system in good working order.
Recommended Repairs: This includes the minimum required repair to get your system running today and recommended service items that I noticed also need attention. I am able to complete these tasks today at a discounted rate, shown below Tear out tri box and Flex from tri box to boot bedroom 1 Flex from tri.box to boot bedroom 2 in Flex tied into boot to try box of new try box. Mastic all connections of entire duct system hanging repaired work job complete customer 100% satisfied
Replace one (1) 18x24x1 filter back return grille. Removed old filter grill installed new filter grill instructed homeowner on its operation.
Technician could not locate source of slight sound but in testing process technician did hear sounds like ECM motor bearings slowly failing. Recommended replacement of ECM motor or replacement of system considering age client has declined at this time.
Customer said he smells something when the unit is running and heat don't work every time they put heat on it blows a fuse. After a thorough investigation I found the ductwork not sealed properly and there is some rodent damage. Also found heat wire to be wired to common wire in the air handler. I fixed the wiring short and cycled the unit in heat. I will recommend we install a germicidal and oxidizer to help with the smell. I also recommend that we seal up all the ductwork and replace at least one run. I gave them a folder and put together a few estimates. I loaded the equipment information to service titan and my pictures. Couldn't get a pic of the coil because the unit is on a metal coffin box and mastic is all over the filter door. I cleared the drain line and left the unit in good working condition in both heat and cooling.
Installed customer supplied nest thermostat. Checked operation. Left system in good working order
Found not heating due to stuck outdoor txv. We will need to check warranty, order, return and replace. System is cooling properly. EM heat will be only source of heating until txv is replaced.
Installed 2 1/2 ton 14 seer split system Amana air handler brand new modified supply Plenum flush copper flush drain reinstalled UV germicidal light installed 5KW breaker heater condenser on existing pad modified copper sealed line set cover performed pressure test performed vacuum below 500 Âµm started up system and charge to factory spec I would recommend having a service tech return on a hotter day to perfect the chartTo perfect the charge a little cold outside to charge perfectly instructed customer on usage of her new AC system double checked breakers 230 amp breakers one for condenser one for air handler customer paid in full customer satisfied
Upon arrival replaced Uv bulb and 45/5 capacitor. Informed about a surge protector to help control the dirty voltage and from having to change out the contactor and capacitor as frequently. Emailed quote over and if and when Joseph is ready he will reach out. Inspected operations. Left system in good working order.
Removed existing AC system and installed new Bryant 2 ton straight cool split system. Performed start up procedures. Left system in good working order.
Replaced evaporator coil under warranty. Vacuumed system. Leak checked. Added 9lbs r410a. Checked system operation. Left system in good working order. Could not get into home to get portable. We will need to return when customers nephew finds key to let us in.
Completed member tune up visit #1. Cycled and inspected equipment. Found uv bulb expired and dual capacitor weak. Will need to return to install warranty 45+5 dual capacitor and uv bulb replacement. Left system in good working order for now.
Uppon my arrival I found the unit had tripped the breaker. I reset the breaker and it tripped again. I checked both motors and they are working properly. The compressor has failed and needs to be replaced. The unit is very old and I couldnt get the serial# of the data tag. Both capacitors need to be replaced as well. The customer is aware of the age and condition of the unit. I recommend we replace the system due to age and overall condition of the unit. I have Cory coming out to give the customer an estimate to replace. Please credit the service call fee towards the new system. I left the unit off at the sub pannel.
Completed tune up on system, I checked all electrical components and motors. I cleared and primed the drain line. Left system running with a 20 degree delta T. Uploaded pictures to service titan. *note* customer said he would renew his TAPS next month
I added 2 lbs of 427a. I replaced filter in attic. The system is on its last leg and very old. The air handler is rotting out and dripping water into secondary pan . The high side is running very high. The system has high blood pressure.. the dual run capacitor is weak. I offered membership and replaced the dual run capacitor, declined. I offered for Corey to come out to give a free estimate. He said we gave him an estimate already. I donâ€™t see it in the work order. We offer 0% financing on system replacement..
Upon arrival found float switch broke. There was a little bit of water in the float. Cleared drain line and replaced float switch. Left system in good working order.