Air Conditioning Repair Pinellas Park FL
We understand how crucial it is to have your AC working at full capacity to give you the most comfortable environment. That’s why AC repair is a serious business and having a perfectly functioning Air Conditioner is so important. No matter how you may try to prevent any issues, it is bound to happen…There is no need to worry. Total Air Inc. provides expert Air Conditioner Tune-ups, AC preventative maintenance, and Air Conditioning Service and AC repair in Pinellas Park, FL and surrounding areas at an affordable rate.
Pinellas Park Air Conditioning Repair Experts
When the Florida heat pumps up, the last thing you need is for your air conditioning system to stop working. Sometimes your AC will act up and when it does, you can count on the quick and dependable AC Repair Service from Total Air Inc. We understand the importance of a fully functioning Air Conditioner and make your AC concerns a top priority.
At Total Air Inc. we are committed to keeping our customers in Pinellas Park and throughout the Pinellas Park area, cool and comfortable. Our experienced and highly trained HVAC technicians will provide the prompt, high quality air conditioning repair service needed to get your air conditioning systems up and running smoothly.
If your Air Conditioning unit is blowing hot air, making strange rattling sounds, or won’t turn on at all, give us a call here at Total Air Inc., (727) 822-7700. We will be there to solve any of your Air Conditioning problems. When it comes to Florida heat, AC Repair is crucial for any situation, large or small.
for Pinellas Park, FL
still no air
Briggs - Pinellas Park, FL
Good service, explained a lot. Unfortunately couldn’t help with air because of bad compressor. So it’s July, holiday, and weekend and we have no air, so it is hard to rate a great experience.
Merritt - Pinellas Park, FL
Very nice job and quick. Very satisfied
Great and efficient service.
Null - Pinellas Park, FL
I will recommend Total Air in a heartbeat 💓.
Professional service. Knowledgeable installation. Much helpful information.
Dolniak - Pinellas Park, FL
Upon arrival replaced Uv bulb and 45/5 capacitor. Informed about a surge protector to help control the dirty voltage and from having to change out the contactor and capacitor as frequently. Emailed quote over and if and when Joseph is ready he will reach out. Inspected operations. Left system in good working order.
Removed existing AC system and installed new Bryant 2 ton straight cool split system. Performed start up procedures. Left system in good working order.
Replaced evaporator coil under warranty. Vacuumed system. Leak checked. Added 9lbs r410a. Checked system operation. Left system in good working order. Could not get into home to get portable. We will need to return when customers nephew finds key to let us in.
Completed member tune up visit #1. Cycled and inspected equipment. Found uv bulb expired and dual capacitor weak. Will need to return to install warranty 45+5 dual capacitor and uv bulb replacement. Left system in good working order for now.
Uppon my arrival I found the unit had tripped the breaker. I reset the breaker and it tripped again. I checked both motors and they are working properly. The compressor has failed and needs to be replaced. The unit is very old and I couldnt get the serial# of the data tag. Both capacitors need to be replaced as well. The customer is aware of the age and condition of the unit. I recommend we replace the system due to age and overall condition of the unit. I have Cory coming out to give the customer an estimate to replace. Please credit the service call fee towards the new system. I left the unit off at the sub pannel.
Completed tune up on system, I checked all electrical components and motors. I cleared and primed the drain line. Left system running with a 20 degree delta T. Uploaded pictures to service titan. *note* customer said he would renew his TAPS next month
I added 2 lbs of 427a. I replaced filter in attic. The system is on its last leg and very old. The air handler is rotting out and dripping water into secondary pan . The high side is running very high. The system has high blood pressure.. the dual run capacitor is weak. I offered membership and replaced the dual run capacitor, declined. I offered for Corey to come out to give a free estimate. He said we gave him an estimate already. I donâ€™t see it in the work order. We offer 0% financing on system replacement..
Upon arrival found float switch broke. There was a little bit of water in the float. Cleared drain line and replaced float switch. Left system in good working order.
I inspected the ductwork. The ductwork is not repairable. The plenum boxes are falling apart and the main ducts and runs are the original metal ductwork. The insulation is falling apart on metal ductwork. Need to replace the ductwork. The office will reach out to you to schedule Corey our comfort advisor to give you a free estimate.. of the system hasnâ€™t had a maintenance, I recommend a maintenance soon.
Performed system tune up. Inspected all electrical components and found no issues. Amp readings, mfds and pressures are in range. Coils are clean . Replaced air filter for my customer. Pure air system is working properly. Cleared the drain line. Left system running.
Upon arrival performed maintenance. Inspected systems electrical components, coils, pressures, and filters. Cleared drain line. Found that the start capacitor had corrosion on it and the dual run capacitor was reading weak. Recommended on replacing both parts, she will discuss with her parnter and reach back out to us on these items. UV light is working. Signed up for a membership and used today as visit number 1. Left system in good working order.
Upon arrival found drain line clogged. Cleared line with vacuum and nitrogen blown through the line. Tested to insure drain was good before departure. Told him about the Evaporator coil being slightly dirty. Left system in working order.
At this time I didnâ€™t catch the blower turning on/off intermittently. Itâ€™s a Ecm motor which the module could be failing. A surge could of caused this. The evap coil needs a clean in place. I recommend on installing a surge protector at condenser from surges and voltage fluctuations. Mark will like to move forward on blower motor for air handler and chemical clean on evap coil. Mark will think about the surge protector. I vacuumed drain line... The office will reach out to schedule appointment. .
Found system operating upon arrival. Found error code stating system lost hi voltage and it dropped below 175 vac. Cycled and inspected equipment. Left system in good working order for now. Recommend: 2-surge protectors for outdoor condensers to help with power fluctuations and surges. Customer declined surge protectors at this time.
Performed complete tune up on AC system. Checked all electrical components, pressures, coils, filter and cleared drain line. System was low on refrigerant so with customer approval we added 2lbs of 410a from jug #147. Left system with 18 degree Split but refrigerant levels will need to be monitored upon next visit. Left system in good working condition.
Cycled and inspected equipment. Found system low on R-410a causing error codes. Also found liquid drier leaking at condenser. Recommend: new liquid drier and adding 4 lbs R-410a. Was not able to complete due to inclement weather. Rescheduled for tomorrow morning. Installed a new filter drier and 5 lbs R-410a. Cycled and inspected equipment. Left system in good working order. Also found filter slightly dirty. Customer stated she will replace 20x22x1.
I inspected the ductwork as much as I had crawl room. There is no masyic on any connections. The supply grills in the floor are sweating. The customer wants to add a supply in the bathroom and her bedroom. I recommend we seal up all supplies with mastic and tape. Also insulate each grill with foam tape . We will need a small guy to go under and inspect where I couldn't get to. I signed the customer to our maintenance program. So we need schedule a tune up asap.
Upon arrival performed maintenance. Inspected all electrical components, coils, pressures, and filter. Cleared drain line. Found the system low on refrigerant. Weighed in 1 pounds of r-427a refrigerant. Recommended on installing a surge protector to help control the dirty voltage going to the system, we did not move forward at this time. Left system in good working order.
Upon arrival found that the compressor had failed due to LRA. I tried to jump start it with higher mfd and start cap but unsuccessfully. Gave two options to my customer, replace the compressor or the entire system. Customer is interested in a system replacement. Left system off.
I cycled and monitored the system and found it was a little low on refrigerant. I added 1 lb of R410A, cycled for proper pressures and temperatures and left the system in good running order. I didnâ€™t charge a service call fee due to we just performed a tune up.
Upon arrival found the system completely out of refrigerant. System is almost 10 years old and in poor condition. Evaporator coil is completely impacted. I recommended charging the system to get her going if she can't wait till Monday to perform a full leak search. Based one the age of the system and the leak I told her that a system replacement may be a better option that provides the most value for her money. She moved forward with me charging her system. When adding refrigerant heard the refrigerant leak, refrigerant is leaking at the electrical terminal of the compressor. Recommendations 1- I highly recommend replacing the system. 2 - If customer declines a system replacement and would like repairs instead, the compressor and the electrical terminal needs to be replaced. There is no way to know if there is further damage to the unit.
We found multiple issues with the system. The evaporator coil is dirty and restricted causing the system to freeze up. Tenant ran the fan for it to thaw out. The condenser coil is dirty and restricted causing the system to run on a high head pressure (425 +). I called Doug and informed him the evaporator coil needs to be pulled, cleaned and the condenser coil needs to be chemical cleaned and then a proper check on the system. I gave him the quote for repairs and informed him of financing options also TAP senior membership because the system really needs to have proper maintenance. He will think about and let us know. ***Note*** The airhandler is located in a closet with a bifold door. Itâ€™s difficult to take the door off and it needs to be removed for the evaporator coil pull and clean. The tenant is aware of this.
Inspected the system and the evaporator coil is dirty and also some of the copper distribution tubing are missing. This looks irregular. The system is running on a high head pressure and low suction. I informed the customer we will contact the manufacturer about this situation and let him know something tomorrow. Probably replace the evaporator coil and the txv. I left the system running and cooling.
When I arrived system was cooling and the symptom was not present, also was storming outside couldn't perform proper service. Told customer to call us if symptom presents it self again. Returned and found that the system was extremely overcharged. Recovered 3 lbs and got the system pressures up to spec. Noticed air leaks at the supply plenum and duct work. Also the house has only one return and has additions to it. I allowed the system to run for a while, my delta T is 20 degrees and pressure are good with proper super heat (piston metering). No more symptoms expressed. Cleared the drain, left system running. Note: offered sealing the plenum but declined. Told owner that if issue returns to give us a call and keep system on.
Customer informed me another company came out yesterday and added refrigerant to the system and told her the evaporator coil is leaking. The emergency drain pan was partially full of water due to a restricted drain line and the evaporator coil is dirty. I emptied the drain pan, flushed and cleared the drain line. I Cycled and monitored the system, checked for proper temperatures and pressures. I recommend pull and clean the evaporator coil because the return plenum is very dirty. They will try to clean the return plenum. They will think about us coming back to pull and clean the evaporator coil and purchase a TAP membership. She also asked about financing the work. We can give them a follow up call in a few days. I left the system in good running order.