Air Conditioning Repair Pinellas Park FL
We understand how crucial it is to have your AC working at full capacity to give you the most comfortable environment. That’s why AC repair is a serious business and having a perfectly functioning Air Conditioner is so important. No matter how you may try to prevent any issues, it is bound to happen…There is no need to worry. Total Air Inc. provides expert Air Conditioner Tune-ups, AC preventative maintenance, and Air Conditioning Service and AC repair in Pinellas Park, FL and surrounding areas at an affordable rate.
Pinellas Park Air Conditioning Repair Experts
When the Florida heat pumps up, the last thing you need is for your air conditioning system to stop working. Sometimes your AC will act up and when it does, you can count on the quick and dependable AC Repair Service from Total Air Inc. We understand the importance of a fully functioning Air Conditioner and make your AC concerns a top priority.
At Total Air Inc. we are committed to keeping our customers in Pinellas Park and throughout the Pinellas Park area, cool and comfortable. Our experienced and highly trained HVAC technicians will provide the prompt, high quality air conditioning repair service needed to get your air conditioning systems up and running smoothly.
If your Air Conditioning unit is blowing hot air, making strange rattling sounds, or won’t turn on at all, give us a call here at Total Air Inc., (727) 822-7700. We will be there to solve any of your Air Conditioning problems. When it comes to Florida heat, AC Repair is crucial for any situation, large or small.
for Pinellas Park, FL
Jennifer - Pinellas Park, FL
He provided many options. He came on time. He was very professional and nice
Raga - Pinellas Park, FL
The technicians were courteous and did the installation in a timely manner. I am happy you guys were able to accomodate me in such a short period of time. My only complain was when I checked behind the filter after they were gone where the leaking with my old AC happened, it was not cleaned up. I clearly remember when the guy who came and gave me an estimation of the price of the entire unit explained to me what they were supposed to do in the installation and that’s to include cleaning and putting something where the water was dripping with the old unit. When I took out the filter, the basin which was put there by the other technician who came to checked the leakage over a week ago was still in there. I don’t think the installer bother to even check below. It was still so dirty and still damp.
still no air
Briggs - Pinellas Park, FL
Good service, explained a lot. Unfortunately couldn’t help with air because of bad compressor. So it’s July, holiday, and weekend and we have no air, so it is hard to rate a great experience.
Merritt - Pinellas Park, FL
Very nice job and quick. Very satisfied
Great and efficient service.
Null - Pinellas Park, FL
I will recommend Total Air in a heartbeat 💓.
Professional service. Knowledgeable installation. Much helpful information.
Dolniak - Pinellas Park, FL
Unit shutting off due to float safety switch being activated. I cleared condensate drain line and got out some growth inside the line. And did a heavy solvent flush of the pvc. This issue may occur again due to a poorly ran pvc line. The exit point outside is being forced upwards about a half of a foot to a foot. If the issue persists I informed the customer we need to consider a redesign of the pvc letting the water flow at a correct pitch right outside instead of running underneath the ground. If we do a redesign we will have to drill through the concrete wall to run it properly.
Found system low on refrigerant since last tech put one pound in. Performed a full leak search with electronic leak detector and could not find any leak. Pumped down system and nitrogen tested to 400 psig and used soap bubbles on joints I could clearly see and could not hear or physically see any leak. Nitrogen pressure was not holding steady indicating there is a for sure leak on system. Put enough refrigerant in to try and hold until office can schedule an isolation leak test on system. I did not have parts on hand to begin doing an isolation test. System is operating left in the off position since homeowner is not home.
Compressor failed. Recommend replacement appt set.
System frozen, thawed. System filter clogged, replaced filter. System low on 410 added 1 lb. unit operating at this time.
Unit has an intermittent blower motor failure. Need to call Monday to get a new blower motor under warranty. I got the blower motor to kick back on and instructed them to call back if it goes off again and Iâ€™ll come back out and put a rescue motor in. Did not charge for todayâ€™s call per Baileyâ€™s instructions. Unit working at this time. 7/13/21 upon arrival replaced blower motor. Inspected operations after. Left system in good working order.
Cycled and inspected equipment. Found system off on safety switch due to a restricted drain line. Cleared drain line. Left system in good working order.
Upon arrival package system not operational technician turn thermostat on, measured refrigerant. High side service valve not operational could not measure, low side shows 60 psi for 410 A system this denotes a major leak along with the need to fill with unknown amount of refrigerant due to that fact recommend replacement of system. Client due to financial reasons and inability to finance system Has declined replacement options, client also declined repair options.
Upon arrival checked motors, electrical components, and pressures. Cleared drain line and added Nubrite to system. DeltaT at 20 degree split. 4 year old split garage system running perfect. Replaced UV Pure x bulb and verified operation. Left system in good operating condition
Air handler inspection complete volts amps are within range this unit is operational at this time. Condenser inspection complete capacitor shows slight below rating for microfarads would recommend replacement. Volts amps and refrigeration within range System could use coil cleaning at condenser this would improve efficiency, drain cleared. Tuneup complete this unit is operational at this time.
Air handler not engaging due to a blow fuse. After fixing that I got the unit running and it was blowing warm air. I put my gauges on and the pressures were rapidly skyrocketing up to 400 psi and equalizing at the same time. I tried to pump down the unit to verify the compressor was moving the refrigerant. The compressor is working and at this point the issue is within the txv metering device being stuck open. We need to replace the txv. It should be under warranty.
Required Repairs: These are the minimum services required to get your system running today and does not include any recommended actions that I noticed. Cycled and inspected equipment. Found dual capacitor failed. Found evaporator coil internally impacted causing water to drip off slant coil into auxiliary pan on vertical unit. Also found air handler cabinet contaminated with bio growth. Installed a new warranty capacitor 35+5.eft system cooling for now. Also system is double filtered which is why customer hasn't noticed as much dripping of water due to washable filter catching water. Recommend: pull and clean with pure air x.
Completed precision tune up on system. Cycled and inspected equipment. Left system in good working order. Customer declined maintenance agreement at this time. Customer informed me this will be a rental property within the next couple of months. Recommend: maintenance agreement and pure air x whole house germicidal unit.
Amana ASX14 AC 2 Ton. Install new air handler on exsisting stand. Install new condensate pump. Install nest thermostat. Install new condensor on new pad. Breaker in disconnect outside needs to be changed to 30 amp (pictures uploaded of disconnect). The liquid line Schrader valve will need to be replaced as well. Customer satisfied!
Sealed all return air leaks that were present on the unit. Taped and glued duct board back to unit and return opening. Vacuumed and cleaned all debris out of the return opening. This return is now %100 leak free, clean, and operating correctly and efficiently at this time.
Office to source 25 feet of three-quarter inch Arma flex once this has been sourced office to contact client to arrange installation date. This service has been paid in full.
Arrived at customers home for a maintenance checkup, upon usual checkup of all electrical components and refrigerant levels we found that system was low on refrigerant and capacitor was not within spec. Customer approved adding refrigerant and replacing capacitor. Cleared drain lines and left system in good working order.
Required Repairs: These are the minimum services required to get your system running today and does not include any recommended actions that I noticed. Customer informed me he had 2 problems. #1 sons room will not cool off. #2 upstairs system no cool. Inspected ductwork on 3.5 ton goodman system downstairs. Found duct work installed poorly causing air restrictions with alot of flex 35-40' long with sags and very little static pressure causing low air flow to other side of home where sons room is located. Found upstairs system with a intermittent failing thermostat. Found fan motor mounts broken and fan blade damaged. Also found run capacitor weak, dual capacitor weak, and contactor pitted. Air handler is 2015 and condenser is 2000. Left system off and scheduled free estimate Monday 8-10 a.m. arrival for a new system for upstairs and new ductwork for downstairs. Recommend: new equipment for the upstairs due to cost of repair, age, and overall condition of equipment. Recommend: new
Completed member tune up visit #1. Cycled and inspected equipment. Found both filters in air handlers dirty. Customer will replace a.s.a.p. left 2 systems in good working order. Recommend: surge protectors
Recommended Service +: This includes the required repair to get your system running today and recommended service to items that I noticed also need some attention. I have also included solutions to extend the life of your system and protect it from future breakdowns. I am able to complete these tasks today at a discounted rate, shown Completed member tune up visit #1. Cycled and inspected equipment. Found system low in R22 and in poor condition. Customer declined quote to replace at this time. Added 2 lbs of refrigerant. Left system cooling at this time.
Upon arrival technician noticed water leaking out of evaporative coil, technician checked overflow switch found water, then checked refrigeration and found it below threshold. Technician recommended 2 pounds for 10 a along with drain clearing and leak stopped. Once this work was complete technician ran system to test and found water again leaking From poorly designed evaporative coil condensation collection pan. This factor plus a decaying evaporative coil made technician give recommendation to replace coil client had agreed. System operational at this time, office to contact client with availability of install of coil. This work has been paid in full.
Cycled and inspected equipment. Found system off on safety switch due to a restricted drain line. Found air handler and immediate duct work with bio growth. Also found run capacitor weak, dual capacitor weak, and contactor pitted. Cleaned air handler cabinnet. Installed a new pure air x, run capacitor, dual capacitor, contactor, and cleared drain line. Left system in good working order.
Amana ASX14 AC 2 Ton tear out old condenser unit replace with new Amana asx14 AC 2-ton condenser on new hurricane pad strap down four corners pipe in splice onto electrical low voltage hookup hot voltage tear out old air handler on hanging kit put a new air handler on new hanging kit new Platinum new return plan on low voltage high voltage copper nitrogen test 250 psi vacuum pump Mike 500 micron start up everything working in perfect condition
Required Repairs: These are the minimum services required to get your system running today and does not include any recommended actions that I noticed. Required Repairs: These are the minimum services required to get your system running today and does not include any recommended actions that I noticed. Recommended Repairs: This includes the minimum required repair to get your system running today and recommended service items that I noticed also need attention. I am able to complete these tasks today at a discounted rate, shown below. Client already installed thermostat technician verified wires were correct, no faults found at unit in operation. Technician found main blower fan bearings have leaked oil within air handler recommended replacement of motor client has agreed. Technician noted micro biological growth within air handler client has declined at this time but high chance this will be done as client has seen the growth herself. Pricing for UV Included. This unit is operating
Cycled and inspected equipment. Found system almost empty on refrigerant indicating system has a refrigerant leak. Found contactor pitted, run capacitor weak, evaporator and condenser coils dirty, air handler and duct work contaminated with bio growth. Customer declined all repairs at this time and requested a quote to replace. Rich is scheduled tomorrow 12-2 for a free estimate. I also informed customer we would credit the 79.95 service call fee if customer decides to move forward itâ€™s be equipment installation. Customer is interested in financing. Left system off. Recommend: new equipment and duct work due to cost of repair, age, and overall condition of equipment.
Cycled and inspected equipment. Found drain line restricted, run capacitor weak, dual capacitor weak, contactor pitted, and immediate duct work contaminated with bio growth. Installed a new run capacitor, dual capacitor, and contactor. Customer declined maintenance agreement and pure air x. Left system in good working order for now. Recommend: maintenance agreement and pure air x whole house germicidal unit to eliminate and prevent bio growth.