AC Repair Treasure Island, 33706
The Florida heat is nothing to play around with. We understand how crucial it is to have your AC working at full capacity to give you the most comfortable environment. That’s why AC repair is serious business and having a perfectly functioning Air Conditioner is so important. No matter how you may try to prevent any issues, it is bound to happen…There is no need to worry. Total Air Inc. provides expert Air Conditioner Tune-ups, AC preventative maintenance, and Air Conditioning Service and AC repair in Treasure Island, FL and surrounding areas at an affordable rate.
Treasure Island Air Conditioning Repair Experts
When the Florida heat pumps up, the last thing you need is for your air conditioning system to stop working. Sometimes your AC will act up and when it does, you can count on the quick and dependable AC Repair Service from Total Air Inc. We understand the importance of a fully functioning Air Conditioner and make your AC concerns a top priority.
At Total Air Inc. we are committed to keeping our customers in Treasure Island and throughout the Pinellas County area, cool and comfortable. Our experienced and highly trained HVAC technicians will provide the prompt, high quality air conditioning repair service needed to get your air conditioning systems up and running smoothly.
If your Air Conditioning unit is blowing hot air, making strange rattling sounds, or won’t turn on at all, give us a call here at Total Air Inc., (727) 822-7700. We will be there to solve any of your Air Conditioning problems. When it comes to Florida heat, AC Repair is crucial for any situation, large or small.
for Treasure Island, FL
Hewson - Treasure Island, FL
Sergey was terrific. He fixed the drain and was very pleasant to me. A/c System is working fine now
Excellent preventive maintenance!
Roy - Treasure Island, FL
Diagnosed a bad capacitor and replaced it. This a avoided the AC breaking down when cooling becomes important in a few months. Excellent professional services provided by Total Air Inc and their technician. I highly recommend them.
Drain line was restricted and tripped the float switch. I flushed and cleared the drain line and float switch with approval. Customer says this has happened about 4 times now with the previous technician they had out. If it happens again, I recommend installing a condensate pump. I left the system in good running order.
Replaced the warranty condenser fan motor, checked for proper voltage, amps and temperatures. I left the system in good running order
Install 2.5 Ton Heat Pump,Units Sit On Balcony, Re Use Thermostat, Seal All Plenums. Price Includes All Taxes, Labor And Permits Installed split system brand new copper line set brand new drain line pressure test and micron to factory specs unit working properly customer satisfied
I performed a complete tune up on ac system. And cleared the drain line with coil cleaner and water. I checked all electrical components and motors. Everything checked out to be in good working condition. The system was a little low on refrigerant ( R410A) I charged it with 1 pound of 410A refrigerant out of jug #126. Customer said that the unit wasn't cooling, the thermostat was set to heat. I switched it to cool and it worked. The customer also said that the thermostat would go blank sometimes. I think it's due to tripped float switch. I cleared the drain with nitrogen. I left the system in proper working condition.
Completed member tune up #1. I recommended replacing the uv light, we installed it in December of 2018 and has poor efficiency. Customer also wants a quote to replace the 12x8 supply grill in the hallway, itâ€™s ugly and some rust. He is on a fixed income and would like to schedule the work for after the first of the month. He would prefer the same tech to come back and do the work. I left the system in good running order. The grille is the wrong type and size. It needs to be a 2 way supply register. (10 x 6 & 10 x 4 for proper sizing). (See picture). He wants us to install the uv light the same time with the register. I replaced the supply grill and the uv light. I recommended a pure air system but he declined at this time.
I went through the low voltage and found that the thermostat has failed. It's a communicating thermostat and we need to replace it with the same type of stat. I told the customer that we will be back when we get a new thermostat for him. Model # of stat is IF99-1292. I collected a service fee. I loaded my pictures to service titan and I entered the equipment information as well.
Found airhandler run capacitor failed. I replaced it. Completed member tune up #2. Cycled and monitored the system in heat and cool mode and left it in good running order.
We checked pressures, added 1lb of 410a to be at factory specs.
Installed a Compressor Defender and a Elite UV system. Prerformed start up and both systems are working as intended. System running at the time of our departure.
Install 4 ton 16 seer heat pump with 5 kw heat strips, unit will be removed by crane customer will pay them separately, near thermostat set up dehumidification, reline plenum, cap platform with plywood and metal install germicidal light. Price includes all labor, taxes and permits